On arrival, checked in with vendor log and store manager. Gained roof access. Hauled condensing fan blade,motor and capacitor up to roof. Turned power off to RTU5 via disconnect. Removed failed condensing fan motor, fan blade and capacitor from unit. Installed new condensing motor, fan blade and capacitor in to unit. Returned 24v connection to contactor. Returned power to unit via disconnect. Unit cycled on in cooling. Receiving a 19deg temp split. RTU5 is operational. Checked out with EMS. Filled out work order. Obtained signature on work acknowledgment.