A commercial customer in Taft California requested service for their walk-in freezer that was leaking oil and making a loud noise. Upon arrival, our technician inspected the system and discovered that the king valve was leaking. Sourced the part locally and was able replace the valve same day. Cleaned up the oil that had leaked and confirmed the system was operating and the correct temperature. Job complete.
Our technician troubleshooted a non-operational handdip freezer in Taft, California. The unit is only a few years old but has had refrigerant leak issues already. After diagnosing the system, our technician confirmed that the leak is inside the sealed walls of the compartment and will need to be repaired or replaced by the manufacturer, as the seal will need to be broken. Recommending fix to customer going forward.
Commercial refrigeration technician dispatched to Taft, CA, in response to an ice freezer not working. After careful inspection, our tech found the evaporator frozen solid due to a stuck defrost clock. Tech repaired and forced defrost, de-iced the coil and replaced the defrost clock. Ice box back to normal operations and ice no longer melting.