Response from RESSAC Climate Control:
Hi Ericka, thank you for the feedback. If there's anything we can do to improve your experience for our next visit, please let us know!
Response from RESSAC Climate Control:
Hello Tim, glad to hear the alarm problem was resolved swiftly!
Dispatched our refrigeration tech to a health center in Torrance, CA, to inspect a down freezer. The Traulsen unit was iced over due to two failed sensors. Replaced the sensors and cleared the ice. Confirmed system dropped back down to freezing and is running normally.
Major HVAC installation project continued today in Torrance, California. All sensors, drain lines and most communication lines. Will return on following scheduled visit to complete installation of the communication wiring.
Dispatched our commercial HVAC technician to a restaurant on Hawthorne Blvd in Torrance, CA. The dining room and bar area heat had stopped working. Diagnosed the Carrier air conditioner and found the wireless thermostat had shorted out. Will need to replace the stat to get the heat working again.
Our Torrance CA refrigeration technician was dispatched to a restaurant to repair their walk-in cooler. The evaporator was iced over, and the evaporator coil was clogged with lint and plastic. Our technician cleaned and cleared away the debris and de-iced the coil. He replaced a broken mounted box temperature sensor, and remounted the expansion valve. Unit is operational for now, recommend replacing the condenser fan motor as it's showing signs of wear.
Fall air conditioning maintenance scheduled for today at a commercial property in Torrance, CA. All heating components tested and deemed safe for normal operations, filters and belts changed. No issues found at this time, PM complete.
Received an urgent request for a restaurant freezer in Torrance California, site reported it was up to 25 degrees. Upon arrival our technician inspected the Traulsen unit and found the whole system badly coated in grease, restricting air flow and fan operations. Will need to quote a complete, deep cleaning to bring this system back to code and normal operations.
Summer air conditioning maintenance scheduled at a commercial property in Torrance California. Filter change and basic inspection only, cleared drain lines as well. Found 3 units iced over, will need to quote additional time to troubleshoot. Site cooling at this time.
On-call tech responded to an emergency HVAC call in on Pacific Coast Highway in Torrance, CA. RTU #5 caused the fire alarm to go off. Fire department had responded. Inspected unit, found the unit's smoke detector tripped. Cleaned and reset detector, alarm off now no other issues with unit found. Confirmed all operations normal again with EMS.
Installation team completed a like-for-like replacement of the air conditioner at a shipping store. Removed existing rusted out unit and placed a new Arcoaire 5 ton. Tested all ops, confirmed site is cooling again with no problems.
HVAC technician dispatched to a juice bar in Torrance, California. AC was not responding to any commands. Inspected unit, found system off due to full drain pan and safety switch flipped. Removed water from pan, blew out and flushed the drain lines to clear. System working again, will recommend a filter change and full maintenance to customer as filters are getting clogged.
Our RESSAC HVAC technician responded to an emergency request for a coffee shop too warm and thermostat blank in Torrance, California. He found the 10 ton ICP unit off with wiring disconnected inside. He reconnected the wiring and traced problem to a lack of 24 volts going to the VFD controller. VFD board will need to be replaced. Left blower motor on for airflow to the store, quoting needed repairs to the customer.