HVAC technician dispatched to a juice bar in Torrance, California. AC was not responding to any commands. Inspected unit, found system off due to full drain pan and safety switch flipped. Removed water from pan, blew out and flushed the drain lines to clear. System working again, will recommend a filter change and full maintenance to customer as filters are getting clogged.