Scheduled a home goods store for approved HVAC repairs today in Tracy CA. Upon arrival, our technician disconnected power from unit at disconnect, removed the old VFD and drivepac board. He then installed the new VFD and board, powered up the system and tested. Unit runs normally again, VFD functional and EMS showed no other issues. Job complete.