Returned to a commercial property in Victorville CA to replace a VFD on the #4 Lennox unit. After wiring in new part, tested all operations and called into EMS to confirm there were no alarms visible on any other air conditioners. Job complete.
A cash loan shop in Victorville California reported their AC wasn't working. Upon arrival, our technician inspected the ICP unit and found both condenser fan motors had bad bearings, and the capacitors were leaking oil, causing the unit to trip on high head pressure safety. Will need to quote necessary parts and schedule a return visit.
While onsite repairs two air curtains for a commercial customer in San Bernardino County, our technician also needed to replace the economizer screens on two York air conditioners. Removed and disposed of old screens, installing new screens on both units. No other problems with these units, job complete.
A grocery store in Victorville CA was scheduled for several HVAC repairs today. Our technician replaced two blower motors on the door air curtains, as well as filters for one unit. Each Powered Aire system was tested for proper function after replacing faulty parts. Both curtain units are running normally now, no more issues to report.
Our Victorville, California, area technician returned to a cash advance shop to complete approved HVAC repairs. Their ICP package system had dirty filters, a cracked belt, and a bad contactor. Unit also had a refrigerant leak on the second stage that the technician located and repaired. Washed condenser coils while onsite. Unit working normally now.