A bank in Westlake Village CA reported that their commercial air conditioner servicing the IT room was down. Upon arrival our technician examined the Mitsubishi mini-split and found it off due to loose wiring. He was able to re-tighten the wiring and start the system back up. Unit is functional again, supplying 45 degree air. Space at 66 degrees.
A cell phone provider in Westlake Village CA reported a water leak that has been ongoing at their store. Sent our AC technician to investigate, and found the air conditioners working normally. Traced water leak back from pipe over the restroom and found that the back-flow check valve for the water heater was leaking. This is a plumbing issue, and the customer will need to call out their plumbing contractor to resolve the issue. Alerted both the store manager and our 3rd party contact to situation.
Our AC tech arrived at a bank in Westlake Village, CA, to perform preventative maintenance on their HVAC equipment. Site has a Mitsubishi server room unit that we service monthly. The tech cleaned the washable air filters, inspected all electrical, motors, coils and tested heating and cooling. No deficiencies found, maintenance complete.
Westlake Village CA, home goods store requested carbon filters be installed due to nearby fires. Tech removed old and installed new filters, cycled units to confirm air conditioners were all running normally.
Quoted a/c repairs were scheduled at a import goods store in Westlake Village, California. Two Carrier air conditioners had damaged belts that had to be replaced. Tech brought new belts onsite, swapped with old and tested both units. Belts fit well, all repairs complete.
Our Westlake Village, CA, repair tech returned to a specialty imports store to complete approved work. Replaced the check valves on a Carrier air conditioner after recovering refrigerant. Pressure tested after install, confirmed no leakage. Recharged and ran unit, confirmed with EMS that site is working normally.
A summer HVAC PM was scheduled for a local bank in Westlake Village, CA. Filters were changed, washable filters cleaned, wiring and refrigerant levels checked. No issues to report, site in good condition.