Approved air conditioning repairs were scheduled for a commercial property in Westminster California today. Upon arrival, our technician troubleshooted the #1 Lennox unit, repairing a switch in the 24v wiring and installing a new control board. #3 up and running. Proceeded to unit #1 to replace the jade economizer controller. After installing the controller, found additional issues with the blower motor spinning in the wrong direction. Corrected wiring to resolve.