Customer has 1/2” copper water line that needs to be capped. Copper water line used to stub up through the roof and was capped. Capped customers half inch copper water line in attic that used to stub up through the roof.
Upon arriving ceiling in dinning room was removed and water lines where exposed. Performed several test and water lines and saw that customer had a 1/2” copper water line that was snapped off. Copper line appeared to go up through the roof where there was another section that was broken off with a old gate valve and 90 connected.
Snaked customers drain from cleanout under utility sink. Customer had large amounts of grease built up in the line causing the back up. Was able to get majority of the grease removed via snaking.