Was able to her line opened. Performed camera inspection and noticed customer had severe root intrusion right before first main cleanout. Sections of Customers cast iron pipe was also corroding away allowing dirt to enter the drain causing the clog as well. Highly recommend jackhammering up this section of pipe and replacing for $1,550. Customer will continue to have these issues until this section of pipe is replaced. Performed spot repair on section of cast iron pipe exiting the house as recommended. Was able to remove large section of roots. Followed up with another camera inspection and noticed customer had another root intrusion where sewer main tied into sewer main by garage. Dug up this section and removed second root intrusion. Recommended to customer to replace remaining sections of cast iron pipe under house and in backyard. Ran camera rest of the length towards city sewer and didn’t see any major issues.