Josh was outstanding
Response from Sears Heating & Cooling:
Thanks for the review!
Balanced refrigerant charge added leak sealant and hard start on York system
Leak at draining system of AH and wanted that fix and a check of the cooling and heating system Fixed and flushed drain system filters clean 2025-1/—2. Cleaned outdoor unit Pressures are good 128/300 Voltage absorption system is is below spec chose bronze Replaced Cleaned outdoor unit Electrical is secure 2014 5 ton Bryant Sticker on furnace Went over safety switch , not interested Offered service contract as well she will consider
Cost to replace air conditioner.
2020 Bryant air conditioner. Found both fuses and breaker blown. Checked compressor and found continuity through all windings. Temporarily bypassed fuses and system fired up normal operation. Went over options on page hb3. Customer chose hb3a. Replaced fuses and completed performance testing. Refrigerant pressure good. Temp split is 19 degrees. All okay at this time.
Installed filter dryer added coupling to leak, double evaluation Replaced voltage absorption system and contraction system Cleaned outdoor unit and added r22 System is up and running with a 20 superheat
Cost to replace air condition
Ac maintenance inspection including cleaning condenser coil, checking electrical connections and cycling equipment to ensure proper operation.
Annual maintenance check on a Bryant air conditioner. Added surge protector to condenser to prevent issues
Replaced failed capacitor under warranty on a Bryant air conditioner
Ac maintenance including cleaning condenser coil, checking electrical connections and cycling equipment to ensure proper operation.
Annual maintenance check on a Comfortmaker air conditioner
Annual maintenance check on a Bryant air conditioner
Cleaned ac system single stage Bryant 16 seer 2018 installed system is clean. Lots of Cotten wood in this location
Gas and go on older Rhee, heat pump ready to go.
Performing maintenance on a 1999 Lennox air conditioner.