Performing maintenance on a. 2020 American standard 2 stage natural gas furnace.m
System is low on charge r22 Bottom option chosen, does realize the system is of age of replacement but want to fill and see how long this will last first time leak Lennox 1987 and is making not the greatest noise due to compressor Filter is clean 79/226 psig Bella is great
Guy is going to wait on furnace check for November and renew when we come to do furnace check Ac 2020 American standard 16 seer
2016 Bryant air conditioner. Completed mechanical, safety, and performance test on air conditioner. All okay at this time. Customer interested not the iwave. Discussed benefits with her and gave her a brochure. She wanted to have installed today. Showed her how to set blower fan to continuous to get max results from iwave.
System was dirty and needed to be clean. Went ver options. Bottom option Cleaned flame sensing system tightened wiring and did a co check System is up and running Single stage 80%
Customer has cracked heat exchanger. Proposed cost to replace furnace
2019 American standard gas furnace and aprilaire 600m humidifier. Found saddle valve closed not allowing water to pass into humidifier solenoid. Adjusted water flow for humidifier and tested unit. Set humidistat at 35%. Performed combustion analysis on furnace. Ppm co 8/11% o2/flue temp 94 degrees. Discussed with customer operation of humidifier. He mentioned he did. It close the saddle valve and was unaware it was there. Saddle valve is set where it needs to be and does not need to closed during off season. Only turn off humidistat and close bypass damper. All okay at this time.
Furnace check on 2016 90% Bryant. 2 stage system. Is running good filter 16-25-1
Quoting replacement from a tanked water heater to a tankless water heater
Flame sensor. Clean. Humidifier is broken and will be fixing it soon. Multiple issues with it.
Performing maintenance on a 2009 Lennox air conditioner. Installed hard start kit to assist compressor on startup, reduce energy consumption and increase life of compressor.
Performing maintenance on Lennox air-conditioner and a trane air conditioner for a home requiring two systems to properly cool. ac repair in grandview, ohio.