Josh did my annual check up on furnace and also installed a humidifier. Josh thoroughly explained humidifier operation and it’s effectiveness. Excellent service.
Enjoyed talking Hvac with our sears rep!
Filter clean 16-25-1. 2013 Bryant 80% 2 stage furnace. Water tank needs a 4” vent for water tank
Performing maintenance on a 2020 comformaker gas furnace.m
Performing maintenance on a. 2004 high efficiency gas furnace.
Performing maintenance on a 2015 good man furnace
1994 Goodman air conditioner. Customer,er mentioned unit not cooling the home. Found evaporator coil frozen solid. Turned system off and set fan to on. Let customer know system will need to be off for 24 hours to thaw. Returning tomorrow between 9-12 to troubleshoot.m
Cost to replace air condition. Cost to install Bryant air condition
2004 trane air conditioner. System low on r22. Found leaks in 2 spot on the evaporator coil. Went over options on page hj1 and hl1. Also discussed replacement. Customer decided to go forward with estimate. Jamie scheduled today between 1-2 pm. Chose hj1 for temp cooling. Charged system to 20 degrees superheat. Temp drop is 18 degrees. All okay at this time.
Ac check first time Capacitor was for below spec cleaned coil 45/5
Ac check on 2006 Bryant. Builders grade system is running
Performing maintenance on a 2020 American standard air conditioner.
Capacitor is out, no cool. Replaced 45/7.5. System needs cleaned but customer is moving American standard 2010
Cost to replace air condition and cost to install furnace
Performing maintenance on a 2020 comfortmaker air conditioner.
Proposed cost to replace air condition as it is under size for the square feet of home
Performing maintenance on a 2015 Lennox air conditioner.