Always good service
Quoted new equipment for customer including Bryant and American Standard units.
Annual maintenance check on a Rheem air conditioner
Annual maintenance check on a Rheem furnace
Furnace repair on maintenance including cleaning necessary components, filter change and combustion analysis to ensure safe and efficient operation.
Performed oil furnace maintenance and safety check
Bi-level house needs a combination of traditional heat pump system upstairs with Ductless downstairs. Advised I would write up a ballpark recommendation. He's only looking for a Ballpark figure for negotiating purposes at this time. Customer is selling the home and is having trouble due to the lack of air-conditioning
Annual maintenance on Lennox air conditioner
Annual maintenance on Tempstar air conditioner
2024 rheem air conditioner. Back to replace transformer. Did not get power. Found broken ground wire and still did not get power. Found melted wires inside light switch for power disconnect. Cut out break and wire nutted unit. Performed quick set up customers new thermostat to test cooling, all okay at this time,
Air conditioner spring maintenance and vent duct size check. hvac repair in johnstown, ohio.
Proposed installation of 80% Downflow or counterflow gas furnace. Bryant, American standard and comfortmaker
Annual maintenance on rheem air conditioner. Installed Iwave. heating and cooling service in johnstown, ohio.