Performed yearly maintenance and safety checks on 80% Bryant furnace. System is running properly and within manufacture specifications at this time with no cause for concerns.
Completed annual maintenance on a 2007 Norton furnace. All mechanical components of the system check out at this time. During testing of the unit the technician found the indoor unit voltage enhancement system to be out of manufactures specifications. Technician presented options hn10a-e. Customer chose option a. Technician verified operation of the unit after repair was complete. No issues at this time. Technician left information pamphlets for the Iwave air cleaner and humidifier options due having a piano in the living room with no humidification system in the house. Customer stated she will go over the information the technician presented and will get back with the office if she decides to move forward with either option.
Found outdoor fan running, compressor was not running diagnostic shows voltage absorption system swollen and dad not allowing compressor to come on quoted HN13A and completed repairs unit is running properly with him in a factory specifications at this time
Performed yearly maintenance and safety checks on 2004 Bryant air conditioning system. System is running properly and within manufacture specifications at this time with no concerns
Completed annual maintenance on a 2014 Rheem air conditioner. All mechanical components of the system check out at this time. During testing of the unit the technician found the initial amp draw of the compressor was out of manufactures specifications. Technician presented options Hn1a-e. Customer chose option A. Technician verified operation of the unit after the repair was complete. Technician recommended surge protector for outdoor unit due to power outages and surges in the area. Customer declined at this time. Customer also raised concern about unit making a rattling noise during operation. Technician found the service panel was loose. Technician tightened service panel and sound went away. No issues at this time.
Perfomed first furnace and ac check on system. System at one point was converted from electric to gas. Installer left old system and installed system 2 ft away. Created huge bypass for airflow. Informed customer that is a issue and both units won’t run properly until bypass is removed. Also informed customer temperature reading won’t be accurate or will I be able to tell how systems are actually running. Found humidifier doesn’t have feed tube and needs new pad. informed he will need a new humidifier. Cleaned both units, found voltage absorption system in furnace is outside manufacture specifications. Also found flue pipe set in boot. No tightening mechanism sealed with thumb gum. Informed customer of health concern. Informed customer possibly a design flaw could be install flaw. Customer hoping furnace and/or ac will fail sooner rather then later due to having home warranty and expecting replacement soon.0ppm co in supply. 9ppm co in flu. Within manufacture specifications as far as I
Returned to look at air conditioning system. Customer stated comfortability is sustainable has concerns for the thermostat numbers getting too far separated. Stated 4 degree once. Informed customer stat has a 3 degree plus/minus. If timed correctly you will see 4 degree difference. Unit is running properly and within manufacture specifications at this time no concerns at this time.
Gave cost to replace central air conditioning. Cost to install air condition, humidifier and ecobee 3
Upon arrival unit was cycled on and cooling found unit running with 20 degree temperature drop. 14 degree sub cooling unit running properly at this time. Customer stated it had frozen up. Stated condenser was layered in debris and filter was dirty. Customer stated he turned unit off for 8 hours changed filter and rinsed off unit. Been running properly ever since. No firther concerns at this time.
Completion Notes: Customer had concerns n new ac system recently installed. Had technician confirm unit is in fact a single stage 14 seer Goodman air conditioning system. Found furnace is a 2 stage gas valve without the ability of second stage cooling. Claimed unit wouldn’t keep house cooled down during higher temperatures such as 85 degrees. Found all registers and return air vent are open and pushing/pulling air. Found 3 ton air conditioner has 8*24 return duct size. Return drop not rated for appropriate air supply to be returned to furnace. Found outdoor unit singly dirty covered in debris. Informed customer possibly a handful of things added up to current situation as well as Honeywell t-6 having a 3 degree plus/minus allowance for set temperature. Customer wanted return replaced with proper size today as well as outdoor unit sprayed off. Called for pricing quoted ho6 for return drop and sh3 for cleaning of condenser. Had proper duct deliver and replaced today. Cycled unit. No furt
Completion Notes: Perfomed yearly maintenance and safety checks on 2013 trane air conditioning system.. found multiple concerns being in voltage absorption unit swollen and not producing capacitance not allowing fan to operate. Presented options hn13 A-E customer chose option c to address fault and add hard start and surge protection systems to unit. Performed repair and cycled unit on. Fan operated upon repair. Found refrigerant low on charge. Informed customer of issue and possibilities moving forward including replacement of evap coil. Leak seal additive, and solely charging system. Presented options HJ7 A-E CUSTOMER CHOSE OPTION b to charge unit and add leak sealant. Performed repair and charge unit. Unit running with 19 degree temperature drop upon departure.
Upon arrival made call for cooling both units cycled on. Technician found outdoor fan running compressor fault to cycle. Found 0 reading at voltage absorption system. Not allowing compressor to cycle. Compressor showing high resistance. Unit cycled on ran with 12 degree temperature split. Found outdoor coil covered in debri. Unit low on charge. Informed customer of issues and concerns gave ball park prices on repairs. Customer failed to answer upon departure left unit in state at which it was upon arrival, customer called back after departure. Interested in quote for new system
Perfomed yearly maintenance and safety checks on 2019 Bryant air conditioning system. Unit is running properly and within manufacture specifications at this time. No concerns at this time. Informed customer of hard start and surge protection system. Customer stated possibly relocating with job so will pass at this time.
Completed annual maintenance on a 2016 Bryant air conditioner. All mechanical components of the system check out at this time. Technician observed initial amp draw outside manufacture specifications. While presenting options customer stated he was not interested in completing repair today.
Technician made call for cool upon arrival. Diagnostic steps show no reading of capacitance, found other concerns including, fins at the bottom of unit smashed n preventing flow of air. Sealant covering penetration hole receding not sealing hole. No surge protection or hard start on unit. Unit coil very dirty needs cleaned. Customer stated he will clean coil and isn’t interested in accessories at this time due to age of unit. Presented option hm13A-B to discuss services and address concerns customer chose option b to replace sealant and armaflex in conjunction with replacing of voltage absorption unit.