Josh did a great repairing my air conditioner. Highly recommend this company.
Ramon is genuinely the best tech I’ve ever had help us before. He really takes his time to explain things to me and makes sure I understand what is happening in addition to how all products work as I typically have a lot of questions haha. Truly, your best employee.
Response from Sears Heating & Cooling:
Thanks so much! We will show this to Ramon and the team!
Performed furnace maintenance and safety check on York unit
Restored furnace to clean condition
Performed air conditioner maintenance on Bryant unit
Performed air conditioner maintenance on Goodman unit. Replaced failing capacitor and hard start
Provided estimate to move AC condenser over 5 feet.
Replaced leaky evaporator coil, inspected Aprilaire digital ventilation system
Found leaky Evaporator coil, provided temporary cooling
Cost to remove geothermal unit and install heat pump system
Performed air conditioner maintenance on York unit
Performed furnace maintenance and safety check on Goodman furnace . Serviced Aprilaire humidifier for heating season.
Performed furnace maintenance and safety check on Bryant furnace
Replaced Lennox 90% drains traps. Fixed popping noise in duct work with s lock. Tied in safety wiring that was not in play and added drain line for pan
Furnace upstairs, there is a leak out of the trapping system, Lennox. There is not back up drain line and the safety system is not wired in. Concern of Greg’s was that there is water build up in the summer time on furnace. Lines could be sealed better, Hf-5 Basement furnace The trapping system is leaking on floor and water dripping on furnace in cooling There is a popping in the supply duct due to not having cross lines will have to add S lock and make lines that are inverted. Hf-5 Wp 35 was very bad replaced Monday is a good day to return to do repairs Furnaces are form 2017 Lennox 90% systems one stage up stairs and downstairs but down stairs has two zones thermostat is next to furnace in basement for zones and main stat is on pillar before going downstairs Co in home is 0ppm but there are multiple fire places running and can lead to co in home Flame sensing systems are clean and no electrical issues in furnaces
Proposed installation cost of furnace with heat pump. Propane gas fuel. American Standard heat pump
Annual maintenance check on 2 Lennox air conditioners