Josh was great! Super knowledgeable and friendly. Will be using Sears again in the future for sure
Performed air conditioner maintenance on Bryant units
Water tank is working I checked combustion, passed tested No leaks Tank is very clean and no dryer in this area Very clean place Flame sensing system is good 2006 BW
Gas furnace 2014 Bryant 80%. I spoke about a Bryant evolution to control humidification is home Wiring would need to change over to communicate
2014 Goodman Bad capacitor. Replace$ 40/5 and added kit 123
Performing maintenance on two 2014 comfortmaker air conditioners.
Provided estimate for new system (heating and cooling). Also for mini split.
Replaced both 201 filters Added tabs to drain in ac drains and mini split Found mini split blower dirty and needs cleaned. Spoke to pat about cleaning of blower and after discount $247. We can do this Thursday if you would like or schedule for a different time
Replaced failing capacitor on Carrier unit
Performed air conditioner maintenance on Rheem unit
Cost to replace air condition
Added start assist to 18 year old unit to lessen amperage draw on compressor startup and lengthen compressor life.
Installed I wave in return duct rise, not enough room inside furnace cabinet. Okayed with customer. Tested unit and set fan to continuous operation to achieve max results from iwave. All okay at this time.
No cool on a 1998 Armstrong Compressor is having a hard time starting up. Added start kit to prolong life
Performing maintenance on 2 2009 carrier air conditioners. Customer mentioned thermostat was blank. Found system showing code 13 for limit lockout. Filter not very dirty. Limit switch stuck closed. Removed limit and loosened to reopen. She said there are some supply vents closed for that system. Let her know to open them, if it get stuck closed again we can replace the limit switch. Customer asking about WiFi smart thermostat. Discussed features with her and showed her options for the t6 pro WiFi for $437 after 10% discount for service club. Also let her know she can purchase her own WiFi stat if she doesnt want to do the t6 pro WiFi. We can install for her $190 after 10% discount for service club. She is going to do some research before making any decisions.
2016 rheem air conditioner. Completed mechanical, safety, and performance test on air conditioner. Found concern with high inrush current to compressor. Recommended adding performance kit reduce inrush current, prevent damage to compressor motor winding and increase compressor life. Showed options on page hn1. Hose hn1a. Completed repair. Amps dropped from 74 to 44. All okay at this time.