Charlie, the service tech, was exptremey knowledgable and competent. We look forward to a long association with SuperTech HVAC Services.
My technician Steven from SuperTech HVAC was great. Prompt, Professional and Polite. He repaired and serviced our HVAC system in record time. I would give this company 10 stars if I could.
Exceptional service. Our Tech, Steven Zhang, absolutely crushed it. How refreshing to witness someone so effortlessly dominate their job. It’s motivating. What an outstanding professional. And what an asset to your company. Thank you very much.
Kenny was so great. He was fast, efficient, and explained the whole system to us! I would call him any time.
Kenny was great. Diagnosed the capacitor issue within minutes and had the unit working in no time. Service-wise, no complaints. However, $300+ for a $20 capacitor is a bit on the pricey side. But I guess that’s the cost of convenience and not having to diagnose the issue yourself or source parts online. Overall, it was a positive experience very and I would work with super tech again.
Daniel was not only courteous and knowledgeable but also quite skilled! He fixed my ac in less than an hour. Super fair price! Ask for Daniel🤘
Steven and crew undertook a difficult replacement with my upstairs unit - great job, very happy, highly recommend!
Charlie repaired a leaking refrigerant line on a commercial Trane Rooftop unit.
Steven fixed a 17 year old heat pump and indoor air handler with a clogged drain line,
Charlie performed a heating maintenance tune- up for Zara in Towson Mall.
Steven was called to diagnosis a water boiler with baseboard heat not working. He found the Kenmore 20 Year old gas heated water boiler has air in the water pipe loops. After Steven conducted water boiler repair, heat is restored.
Steven conducted water boiler repair and restored heat.
We performed a commercial roof top cooling maintenance. We checked all electrical and mechanical components and changed filters.
We performed a cooling maintenance on the 3 year old Trane commercial rooftop unit.
Ac not cooling. Tech replaced motor wheel and now AC works.
Tech performed diagnostic of cooling system. Found that condensate pump was bad and float safety was turning unit off. Recommended replacing condensate pump.