Exceptional service. Our Tech, Steven Zhang, absolutely crushed it. How refreshing to witness someone so effortlessly dominate their job. It’s motivating. What an outstanding professional. And what an asset to your company. Thank you very much.
Kenny was so great. He was fast, efficient, and explained the whole system to us! I would call him any time.
Kenny was great. Diagnosed the capacitor issue within minutes and had the unit working in no time. Service-wise, no complaints. However, $300+ for a $20 capacitor is a bit on the pricey side. But I guess that’s the cost of convenience and not having to diagnose the issue yourself or source parts online. Overall, it was a positive experience very and I would work with super tech again.
Daniel was not only courteous and knowledgeable but also quite skilled! He fixed my ac in less than an hour. Super fair price! Ask for Daniel🤘
Steven and crew undertook a difficult replacement with my upstairs unit - great job, very happy, highly recommend!
Found the heat pump system was not running properly. Heat Pump Service.
Performed Air Conditioning system tune up for customer.
Came to address Issues for heat pump off and capacitor has field for compressor due to clogged condenser coil. AC repair, Replace Dual Capacitor, Chemical Clean Condenser Coil. Replaced Filter.
Arrived and found ants in the contactor. Cleared ants and cycled system to confirm operation. Performed cooling maintenance on Gas Furnace and Air Conditioner.
Arrived and found the system undercharged. Customer was having issues with the system freezing up. Due to age and leaking problem recommend replacement.
Came and address issue on the Air Conditioning Unit not running properly. Found out that the condenser located in a closet with the screen door closed. Closet is building up heat that cannot be released. Informed customer that door must stay open to let condenser breath.
Came and address the issue on HVAC system not running. Found disconnect wiring. Repair wiring on Lennox Gravity Gas Furnace, system working properly now.
Arrived and investigated water was leaking from the flue pipe. Noticed outside along the base of the chimney there was caulk that is cracked and holes are open for water to access. Most likely going into the chimney and running down the flue pipe. Furnace Repair, system working properly.
Arrived and found breaker tripped for heat pump. Heat Pump Service.
Arrived and address the issue on frozen coil and AC not cooling. Air Conditioning Repair.
Came and address the issue on system low on refrigerant. Heat Pump Repair, Add R-410 Refrigerant. Flush Drain Line