One man one hour
Replaced GFI outlet
Checked filter, checked thermostat, checked elements and blower, checked evap coil, checked drain pan and blew out drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coils. 1 system: 2017
cleaned vents, sanitized return, and UV light installed, pre-paid
Changed filters, checked thermostat, checked evap coil, checked/tighten electrical connections, checked fan amps, checked capacitor, checked pressures, cleaned condenser coils.