Quoted job for hot tub 1850
Did home inspection and changed out five gfi
Moved fan box to center of room
Customer resolved issue on his own
Replaced motion light
30 foot of the PVC conduit 90 feet of THHN #10 1/15 amp 2 pole breaker
Replaced bad ballast in light fixture.
I performed the seasonal maintenance per agreement. The downstairs is 11 years old. I recommended replacing the system due to cost of future repairs,age condition and r22 phase out. They are planning on replacing it soon
David called and had her reset the reminder
Changed filters, checked thermostats, checked heating elements and blower amps, checked evap coils, checked drain pan & blew out drain line, checked/tightened electrical connections, checked capacitor (compressor side 35uF and it has 32.5uF), checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coils. Entered Trane air handler manufacturing info. Customer renewed membership last week. 1 system: 2012
Warranty call. Per Ruud factory rep. I replaced the high pressure switch, installed a new defrost circuit board and changed the filter drier. Pressure tested braze joints with nitrogen. Pulled a vacuum and weighed in factory charge of r410a refrigerant, then charged system to proper subcooling. Injected ac renew into refrigerant system. The unit made the noise once and hasnâ€™t made it again. System and defrost operation is significantly quieter. Told client the system will need 24-48 hours for the ac renew to properly circulate throughout the entire refrigerant system.
Checked filters (Customer is changing), checked thermostats, checked elements and blowers amps, checked evap coils, checked drain pan and blew out drain lines, checked/tightened electrical connections, checked blower capacitor, checked capacitors, checked fan and compressor amps, checked pressures and reversing valve (2015 unit was a little low), and checked condenser coils (No outside water). 2 systems: 2015 & 2013
I performed a one time clean and check. All amps,volts,capacitors and pressures are withen specs.
Inspected wiring and devices damaged from flood. Worked up quote
Tripped GFI for landscape lighting transformer. Reset.