completed tune up, with coupon $59 and added 2 pounds of refrigerant
coil has been replaced, and system is working good, office will call to collect payment
Performed routine maintenance on 2016 system checked heat strips checked blower motor checked condenser motor checked capacitor checked contactor checked temperature checked pressure checked drains cleaned both coils unit is working OK at this time
Performed routine maintenance on a one-year-old system checked heat strips checked blower motor checked condenser motor checked compressor checked contactor checked capacitor checked pressure checked temperature checked drains unit is working OK at this time
Preformed service call on 2015 ruud system system is working properly at this time
installed evaporator coil on 2011 amana system system is working properly at this time
Preformed service call on a 2011 amana condenser matched with a 2011 Goodman air handler I found leak in evaporator coil the coil will need to be replaced
2014 Ruud system- checked system amps checked blower motor and blower wheel checked evaporator coil and clean evaporator coil checked wiring checked fan motor checked compressor checked contactors and capacitors checked float switch checked heat strips checked condenser coil and clean condenser coil checked system charge.
One system is a 2017 one system is a 2014 in the other system is a 2014 done maintenance on all three systems and all three systems are working good two systems are underneath the house actually three checked everything and made sure everything was working good
Install valve and check system out and make sure system is working good he said he will let us know if it happens again
Performed routine maintenance on 80% gas furnace and straight AC condenser furnace is about three years old check flu checked safeties checked gas valve checked inducer draft motor check blower motor check burners Clean coils checked condenser motor checked compressor checked capacitor checked temperature clear drains unit is working OK at this time
Performed routine maintenance on to your old Ruud gas furnace and condenser checked flue checked safeties checked gas valve check burners checked blower motor clean coils checked condenser motor checked compressor checked contactor checked capacitor checked pressures checked temperature unit is working good at this time
Service agreement clean and check on an 8-9 year old split heat pump system. Washed and waxed outdoor unit. Cleaned pine needles and debris from the bottom of the unit out. Cleaned evaporator coil in attic. Flushed out drain line . Brushed out debris from electrical compartments. Cleaned out biological growth in air handler cabinet. Checked refrigerant , mechanical and electrical operations. Amp draw on compressor is high on start up. System is operating at this time. Recommend a start booster to cut down on compressor start amps, a kool Kap to keep debris out of the unit and a stay clean strip to keep the drain running freely. Home owner is not here.
Serviced both systems 2008 models. Downstairs needs to be replaced due to condition. Upstairs is in fair condition overall
I need instructions on how to put this valve in