Roto brush source removal and sanitized complete duct system.
Duct cleaning and uv light,must be done Monday before the painters paint. The office had transferred the phones, I talked to Chris about this.
I checked the system and all components in cooling. I recommend a duct cleaning due to dust build up in the duct work,I also recommend a sta clean strip to regent clogged drains and odors. System 7-8 years old. Rental property. Owner not there.
The duct work and dampers have to be moved. John knows the details
I cut the backlight on continuous.
I performed the seasonal maintenance. One time service. Recommended investing in a service agreement system 1-2 years old
To repair a leak in the true suction line and recharge the system
Changed filter, checked thermostat, cleaned burner assembly and other gas components, cleaned gas burner blower capacitor (low), checked capacitor, checked blower amps, checked fan and compressor amps, checked evap coil, checked/tightened electrical connections, checked pressures, cleaned drain line, cleaned condenser coils and unit. I gave customer service agreement plan options, she will call the office to renew. 1 system: 2016
Gave quote to change out meterbase.
Prepaid Preventative Maintenance: Verified System Pressures, checked heating strips operation, verified airflow in cooling mode. Changed filters, cleaned condenser coil, cleaned drains, verified amp draw at compressor. Changed out filter & recommended using NON-Pleated filters for higher efficiency. Raised fan speed from low to med-high for nominal efficiency with new duct work. No problems found, system & ductwork is in excellent condition & operating efficiently!
Prepaid Preventative Maintenance 1 System (4 mini Split heads & 1 Condenser ) - Verified amp draw, checked pressures in cooling, Verified fan operation & cooling efficiency. Cleaned out drains & verified incoming voltages. Cleaned condenser coil, filters, & checked for any obvious signs of Refrigerant leaks, but found no issues. Units are in excellent condition running very efficiently!
Took a picture of the thermostat for warranty purposes
Failed compressor & undersized breaker (was 20 amp, should be a 25) - Need to get electrican to change out 2 20 amp micro breakers & 2 25 amp micro breaker on sub panel & quote price for new compressor (pending warranty status) To get unit operating again. ONLY HAS ELECTRIC HEAT UNTIL COMPRESSOR IS REPLACED & BREAKER IS FIXED See photos for model/serial
Changed filters, checked thermostats, checked elements and blowers, checked evap coils, checked drain pan, blew out upstairs line, checked/tightened electrical connections, checked pressures and reversing valve, cleaned condenser coils, checked fan and compressor amps. 2 systems: 2016 2 mini: 2006 & 2015
The compressor is shorted to ground. We need to check warranty and get a price and call with the info.