Installed generator outlet 30 amp breaker interlocking kit
Installed new bathfan in place of can light in bathroom. Took out all old ductwork and connected the main line to exhaust fan. Removed all materials from site.
Have to look up prices of materials for quote.
Changed out two disconnects Two Whips edit 1/35 amp breaker 1/45 Qo
Electrician tested all lights switches and receptacles found one issue with open neutral repaired it and replaced ballast and downstairs storage room light all checks out well warping of vinyl siding was not caused by wiring issue
Wrong size wire feeding irrigation pump.
Installed receptacle for dishwasher.
Quote for work to be done. Will contact customer with quote
Roto brush source removal and sanitized complete duct system.
Duct cleaning and uv light,must be done Monday before the painters paint. The office had transferred the phones, I talked to Chris about this.
I checked the system and all components in cooling. I recommend a duct cleaning due to dust build up in the duct work,I also recommend a sta clean strip to regent clogged drains and odors. System 7-8 years old. Rental property. Owner not there.
The duct work and dampers have to be moved. John knows the details
I cut the backlight on continuous.
I performed the seasonal maintenance. One time service. Recommended investing in a service agreement system 1-2 years old
To repair a leak in the true suction line and recharge the system