Performed Routine maintenance check heat strips checked blower motor checked condenser motor checked capacitor checked contactor checked compressor checked pressure checked temperature Cleaned both coils unit is working OK at this time
Performed routine maintenance on 2017 traine system checked heat strips checked blower motor checked condenser motor checked capacitor checked compressor checked temperature checked contactor checked pressure cleaned both coils unit is working OK at this time
I checked both systems per agreement. I recommended installing sta clean strips in the drain pans. I also explained there purpose. Homeowner declined my recommendations. I also gave estimates on 2 WiFi thermostats per homeowner request.
Performed routine maintenance on 2016 Goodman system checked heat strips checked blower motor checked condenser motor checked capacitor checked compressor checked contactor checked pressure checked temperature cleaned both coils unit is working OK at this time
Replaced 5 customer supplied switches.
Service agreement clean and check on a 12 year old split heat pump system. Picked up key at office and dropped it off when I was finished. Cleaned entire system. Filter there is clean. Changed batteries in clients thermostat they had there. Thermostat had a circuit board glitch and wasnâ€™t responding properly until I changed the batteries. Checked all mechanical and electrical operations. Cranking amps on the compressor are high. Recommend a start booster for the compressor to lower the start amps in order to help extend the life of the compressor. Left message on machine , set thermostat back down to 50 and locked the door.
Diagnostic call on the 12 year old split heat pump system that takes care of the back part. Clients said circuit breaker keeps tripping. Turned system on and reset breaker. Compressor is making a grinding noise then kicking out. Tried putting a start booster on it but the compressor trips right away. Windings in compressor are bad. Quoted clients price and availability for a new compressor and the investment price on a new system. Client needs to speak with the other owner to see weather or not they want to repair or replace the system. Client will let me know as soon as he speaks with him, he was unable to get in touch with him at this time. Client asked about getting the diagnostic waived if they invest in a new system and per the manager we would do that.
Did system check found a nest thermostat wired correctly and set up correctly though thermostat is not making connection to the reversing valve so system is running in heat all the time customer is going to return his nest thermostat for another unit functions normally When reversing valve is activated
Replaced 18 receptacles at the stylist stations.
Installed new fan motor on 2014 amana package unit system is working properly at this time
Performed routine maintenance on 2015 mortex and Goodman system Checked heat strips check blower motor clean coils checked condenser motor checked compressor check contactor checked capacitor checked temperature unit is working good at this time
Performed routine maintenance on 2015 carrier package system checked heat strips checked blower motor checked condenser motor checked contactor checked compressor checked capacitor cleaned the coil checked the temperature checked pressure unit is working OK at this time
Preformed system maintence on 2014 ruud system checked wire connections, amp, draws, air filter, duct work, coils, capacitors, and drains. I cleaned coils and drains system is working properly at this time
Preformed service call on 2014 amana system found system needs a new condenser fan motor