Helped Michael cut in attic fan.
Installed disconnect for A/C unit. Hooked whip up to unit. Replaced 2pole 30 amp breaker with 35 amp breaker.
Replace battery in generator customer wants appointment made after hurricane for tuneup on Generac generator
Added junction box call disconnect change GFI receptacle one 6 foot Quit
1/35amp One disconnect one 6 foot whip
Replaced #10 thhn wire to #8thhn wire for the EV charging station. Replaced 30 amp breakers with 2-40 amp breakers for EV charging station.
Trenches down the pipe for EV charger.
Wired sign up and separated it to its own circuit. Installed ground screw in red box for waffle iron. Installed 4x4 Extension ring on metal box for sign. Installed two stainless steel decor plates for gfi receptacles.
Fixed receptacles for inspection. Changed route of power to sign.
Repaired loose box
Inspectors list: uncover part of trench to see depth of pipe. Strap pipe to building. Strap mc cable from panel wall to receptacle location.
Performed Routine maintenance check heat strips checked blower motor checked condenser motor checked capacitor checked contactor checked compressor checked pressure checked temperature Cleaned both coils unit is working OK at this time
Performed routine maintenance on 2017 traine system checked heat strips checked blower motor checked condenser motor checked capacitor checked compressor checked temperature checked contactor checked pressure cleaned both coils unit is working OK at this time
I checked both systems per agreement. I recommended installing sta clean strips in the drain pans. I also explained there purpose. Homeowner declined my recommendations. I also gave estimates on 2 WiFi thermostats per homeowner request.
Performed routine maintenance on 2016 Goodman system checked heat strips checked blower motor checked condenser motor checked capacitor checked compressor checked contactor checked pressure checked temperature cleaned both coils unit is working OK at this time