Installed new exhaust fan light combo in guest bathroom
helped Kevin Mauldin with line set replacement, monies collected on invoice #32689117
Cleaned and santized vents. Install UV light. *3 vents could not be done.
I installed a uv light kit during the service. Complete. One system is 2018 the other is a 2013
Iâ€™m went into the settings in the thermostat and went to wireless manager so the sensor could be added to the network
The dehumidifier is freezing up. There is no pressure ports to check pressures. The dehumidifier will have to be pulled out and took to the shop,a line tap installed and a leak test done. Need to call the mfr to check warranty info first
Looked at wiring for air handler
Warranty call. Installed new low pressure switch. Need to order a new suction line king valve as well. Office is ordering part. This is from the 15 seer upstairs system.
After rechecking the system Mike has decided to replace the outdoor unit due to a faulty compressor.
Warranty call. Insulated drain line from installation. Checked over noise on air handler. There was only one screw holding the heat strips on. It was rattling. Put the other 3 screws on and itâ€™s not vibrating now. System is operating properly without noises .
I checked the main system and the mini split. The condenser motor sounds like the bearings are going out. I recommend replacing it before it fails. System 7years old. Homeowner not interested at this time
I replaced the upstairs zone damper motor and checked the operation. Complete.mr smicklas for the office to call him for payment.
One time tune up. Client has a leak in their evaporator coil. They said the electric bills have been high. Showed client the leak. Repairs to system are costly. Clients are going to invest in a new system, refunded the money back off the tune up from the system.
I performed the seasonal maintenance on the mini split only. The system is clean and operating properly. Jonathangray also checked all functions on the remote. Installed 2017. one time service
Service agreement clean and check on a 1 year old and 6 year old split heat pump system and a mini split heat pump system. Washed and waxed outdoor units. Cleaned evaporator coils. Flushed out drain lines. Brushed out debris from electrical compartments. Tightened all electrical connections. Refrigerant charges are good on all 3 systems. Checked all electrical and mechanical operations. Installed 2 large stay clean strips in the drain pans. 2 stay clean strips