Installed cable line and outline for workout room
Quoted job for 498 will take one man three hours
Moved two lights
After performing whole home inspection ,.electrician found three receptacles in living room not working .bunkbed bedroom on left outlet showed open neutral in outlets switch at front door has no power not working . Estimate on repair issues found 339.00 plus tax
Signed service agreement to have house electrically inspected.
Tech was called out to homeowners house via home inspector said that the condensing unit was on a 45 at breaker and it was supposed to be on a 40 amp breaker after inspecting panel tech found that the condensing unit is only 40 amp which is what was required and the air handler he was on a 45 amp which is what is required Home inspector give false information
Service agreement clean and check on suite 4 , the hair salon. Put numbers in the system and stickers on all equipment. Washed and waxed outdoor unit. Flushed out drain line with nitrogen and water. Cleaned out primary drain pan and evaporator coil. Tightened all electrical connections. Brushed out debris from electrical compartments. Checked refrigerant, mechanical and electrical operations. System is operating but showing signs of age and Ware.
Service agreement clean and check on suite 2. Washed and waxed outdoor unit, cleaned evaporator coil , flushed drain and cleaned primary drain pan. Tightened all electrical connections. Brushed out debris from electrical compartments. Checked refrigerant, mechanical and electrical operations. Installed a new start booster for the compressor. System is operating at this time but not as reliable due to age and Ware on the system.
Installed four cans in the kitchen. Also put the four cans on a switch.
Checked filters, checked thermostats, checked elements amps, checked blower amps, checked evap coils, checked pan & drain lines, checked/tighten electrical connections, checked pressures, checked capacitors, cleaned condenser coils. 2 systems: Lennox-2016 & Goodman (Canâ€™t tell year-R22)