Quote for ductwork approved
Replaced defrost board and sensor tested system up and running properly
Found a short on the T-Stat wiring corrected found the defrost board that will put in a return for part
From gas to electric
Found thermostat not functioning properly. Installed t6 pro. Tested operation.
Preformed first prepaid maintenance on a heil package unit, model and serial numbers match in system. Checked filter and checked pressures checked amp draws and checked wiring connections. Cleaned coils and added algecide treatment to drain pan. Checked all braze joints and checked temperature split. Unit is operating properly at this time. Recommended and installed Blue Tube Kit for growth prevention.
Preformed first prepaid maintenance on a Goodman split heat pump unit, model and serial number match in system. Checked pressures and checked amp draws, cleared drain line and cleaned coils. Added algecide treatment to drain pan for drain line prevention. Recommended and installed Blue Tube Kit for growth prevention. Unit systematic components are working properly at this time.
Duct Cleaning Cook Registers 7 Returns 2 1 return + 6 registers= $399 Any extra registers +29 Any extra returns +99 Extra Registers - 1x29. = $29 Extra returns - 1x 99 = $99 Total = $527 After discount You pay: $421.60 Will pay when duct cleaning is complete.
Arrived due to stuff coming out of the registers when the air is on. Checked and verified all duct work and system is sealed off. There is not entry points sucking any of the dirt/ insulation from attic into the system to blow out. Whatâ€™s coming out of the registers seems as though it was from the change out. Debri got into supply and is blowing into the home. Set up a duct cleaning for thurs. client will pay at completion of duct cleaning. *** please call client when otw!*** ***please use front door***