Excellent! Solved the problem.
Ignacio explained all alternatives well and was a pleasure to work with. A++++
I called to schedule maintenance for our furnace. They were able to schedule me the next day for service. The technician Ty showed up on time, was polite and quick and efficient in the work he did. I feel like the price was fair for the service and small repair needed.
I called Thompson, because my ac went out, and I needed someone quick, due to my compromised immune system. They told me they could have someone out, same day within 2 hours from the time I called. Amazing! Ty was the tech, and he was awesome. Explained everything to me, waited while I called my husband to let him know what the problem was, and was able to get us up and running. He does need to come back with a part that he has to order, but at least my ac is working again for now. I’m really impressed by Thompson, and Ty, and would highly recommend them!
Quality professional service. Quotes are accurate and final costs in line. Notification and picture of plumber doing service before arrival. Complete clean up after repair. Availability has been great!
One of the most professional technicians we have had to address plumbing issues. Recommend him without any reservations.
Auger clogged toilet Burst pipe pin hole leak 1/2â€ copper pipe Replace section thatâ€™s been exposed
Run snake thru clean out access, run until we can see it go thru to septic tee area. Ran thru a blockage close to the septic tank. Ran a camera thru, no additional charge. Camera was going up thru a combo fitting for a clean out access, before that found the pipe to have standing water in it. Recommend customer to remove the pavers to get access to cleans out for us to camera up stream to see whatâ€™s causing the issue. Only warranty for today as there is a issue causing back up. Recommend camera and go from there. Escondido area.
Performed a heating maintenance in Escondido.
Conduct a slab leak inspection and find out which hot line is leaking and where does it go to. Customer approved work over the phone.
Replaced a auxiliary limit switch and completed a heating maintenance in vista
Replace customer supplied cartridge
Whole house filter install by outside water meter service area. Install new filter with brass fittings and reconnect supply lines. Retest and Check for any further leaks. Installed and tested, all working great. Installed under kitchen filter as well. No leaks. Cut out leaking tee on pvc line for customer, no charge.
Performed a heating maintenance in oceanside. Very old 60% furnace recommend replacement.
Removed old equipment, installed New furnace, coil, and condenser were installed. To include high voltage disconnect and thermostat. Equipment was tested in both heating and cooling. Customer was given a walk through of work done and basic thermostat functions. AC/ FURNACE change out Escondido,Ca
No issues. Jumped out system and worked as should. Tested system from thermostat and worked as should. Temp rise of 38 permissible is between 30 and 60.
Issue no cooling. Diagnosis: bad thermostat. Replaced thermostat and tested system. System functions as should.
Heating and cooling maintenance in oceanside. System is low on refrigerant. Replaced motor run cap. Replaced thermostat per customer request.
Upon inspection found the gas flex lines to grill were under sized causing a burner to go out when others are on. Recommend re sizing piping with bigger gas flex and gal piping. Process of elimination, fix the issues and if it still happens then we can get in contact with manufacture on their regulator. Tested with new piping and parts. All burners working great. Customer approved and was happy with work. No leaks.
New 8ft dishwasher water line Install dishwasher Install air gap 2 Leaking p traps attempt to fix Shower valve not getting hot Attempt to fix
Customer would like new toilet in master bathroom. And clean out shower drain. New glacier bay toilet was installed in master bedroom. Shower drain was full of hair and sludge.