As always , they always fit us in the schedule and never make us wait !
Thompson plumbing presented estimate to customer to move washing machine from upstairs into garage. Customer will think about estimate in Caliza back to schedule if needed. Estimate is only good for 30 days
Performed maintenance on gas furnace. System is operating to specs 3 to 5 years old
Install Noritz NRCR92 tankless water heater. Our scope of work includes, the venting of the new water heater through existing roof vent. We will install a neutralizer on the condensation drain line. We will tie into existing recirculation line and set the internal tankless pump. We will dispose of old water heater.
Thompson plumbing is researching availability and cost of unit. Customer will call us to schedule if we can give him a discount. Will is working on it.
Estimate to replace the systems.
Replaced furnace in closet and AC unit outside
Customer had low flow coming from the upstairs guest bathroom. Installed a new Delta shower cartridge and cleaned out the shower valve. Found small rocks of hard water blocking the hot water outlet. Also found Teflon tape in the shower head. Turned on water and shower was working as it should.
Performed the heating maintenance on four systems. Upstairs unit has an over amping gas valve. Kitchen unit has a crack in the heat exchanger and that system is too be replaced. No issues with the other two systems. System to be replaced is located to the left of the entry door of the main house and the condensing unit is to the left coming down the driveway next to the propane tank. Replace the office thermostat for free with customer supplied thermostat.
Arrived for no cool. Found grounded compressor. Also found evidence of gas leak on upstairs system. Left gas valve off as precaution. Units 21 years old.
Called for water leak issue. Upon investigation found no signs of leak due to AC. Tested primary and secondary drains with both working properly. Unit 6 years old.
This estimate is to partially rebuild the toilet downstairs, we would then cable the shower in the upstairs master bathroom. We performed the work as stated above We checked for leaks and proper function No leaks Downstairs toilet is functioning appropriately at this time Upstairs Master Shower is draining appropriately at this time. 30 day warranty on toilet repair Additional $178 charge is from a previously unpaid invoice - Additional notes - We found the information for the widespread faucets located in the upstairs master bathroom. The faucets are under Deltas Lifetime warranty and recommend the homeowner contacts them in order to get replacement parts and or replacement faucets
System was low on refrigerant and had a very dirty condenser coil. Chemical cleaning on the condenser coil might be required in the future.
Performed AC maintenance
Estimate is for abandoning leaking 1” gas line under outside bathroom shower. This is the 4th gas leak that has been located by CPL and Thompson in the last two weeks. Thompson plumbing would cut out a small concrete square near outside bathroom and install new 1” gas raiser with 1” isolation valve. Thompson will then run new 1” galvanized pipe up and over around bathroom wall and drop down near new 3/4” isolation valve behind shower wall. Thompson will bubble test work before turning gas back on. Thompson will backfill hole in grass area rough patch concrete square and strap new lines.
Thompson plumbing found another leak in between water heater and laundry at tenant Juan’s house. Thompson recommended cutting out bad section of galvanized pipe and installation of new galvanized pipe and fittings. After 3rd leak is repaired Thompson plumbing can pressure test and schedule for inspection. Thompson plumbing replaced 3/4” gas valve at Juan’s house near water heater. Shut off gas valve. Pressure tested from gas meter. Pressure slightly drops a quarter pound in 15 minutes. Thompson plumbing updated Candy. Thompson plumbing will schedule CPL to return and perform a second leak detection. It’s very possible there might be another leak underground. Thompson plumbing replaced a section of leaking 3/4” galvanized pipe and fittings that service water heater stove and dryer. Thompson plumbing installed new 3/4” isolation valve. After repairing the 3rd gas leak. Thompson pressure tested entire gas line from meter to 1st repair at cricket room Juan’s house near laundry and w