Leaking humidifier, humidifier pad had not been replaced in quite some time. This caused humidifier hose to become clogged with debris and not work properly. Also humidifier was set to wrong setting of "summer" during winter season. Replaced filter, recommended a newer more efficient humidifier to save cost on electrical bills, and cleaned out humidifier line. Humidifier operating properly at this time. Informed customer on settings and how to replace future filters if they decide to stay with this model.
Commercial Lochinvar boilers
Change existing supply boots from circular to rectangular (3 total), and run (2) complete supplies to the living room ceiling. Air handler installed with uni-strut bracket system. Move existing York condenser.
Variable Speed Motor replacement. Install new blower motor and module and reinstall housing motor unit. Program module to match furnace system and reconnect motor into furnace. Cycle to make sure motor is operating properly and cycling air correctly.
Fix leak in piping for Weil McLain boiler.
Scratched flame sensor in Carrier furnace needs replacing.
Crown boiler making hissing noise.
Clogged filter on Artmsrong furnace.
Carrier furnace system making a rattling noise.
Clean and check on Bosch boiler.
Boiler and furnace repair and replacement service. Diagnose and perform annual heating maintenance on Lennox HVAC unit. Inspect heat exchanger for deterioration. Check fan switch. Clean and adjust pilot assembly, replace air filters. Furnace maintenance complete which will help lower heating cost for residential customer. Boiler system is now ready for the winter weather.
Crown boiler not switching on.
Completed new Amana heat pump installation with Aprilaire air filter.
Replaced furnace board on Amana furnace.
Boiler repair. Boiler replacement