Air Conditioning repair for a residential client. Air conditioner not working to cool the home. Technician sent to diagnose and repair. Blown fuses in the unit. Replaced fuses. Cleaned coils and condensate drain. The system is now cooling the home as it should.
Air Conditioning Repair for a residential client. Technician sent to troubleshoot. Refrigerant leak at suction solder point to the common port. Leak repaired. Refrigerant recharged. The system is now operating as it should for the homeowner.
Air conditioning maintenance for a residential client. Technician sent to ensure the system is operating as it should for the homeowner. The coils are clean, The drain line is clear. The amp draw on the motors and compressor are within specs. The contactor and capacitor are good. The freon levels are within specs. This system is ready for the summers, contactors, and freon levels are within specs.
Residential homeowner with indoor air quality concerns. Technician sent to inspect. Dirty ducts causing excess dust to form in the household. Whole-house ductwork cleaning performed. Air filters replaced. The problem has been resolved for the homeowner.
Residential Air conditioning repair. Technician sent to repair. Evaporator coil burnt out on a 4-year-old Goodman system. Evaporator coil replaced. The unit is operating as per the manufacturer's specifications.
Toilet installation for a residential clients' half-bath. Old toilet removed. New wax seal and toilet flange installed. New toilet installed and bolted down.
Tankless water heater installation for a residential customer looking to conserve energy in their vacation home. Installation of the new Rheem tankless water heater system was performed. The customer is happy with the new system.
Heating repair for a residential customer. Technician sent to inspect and repair. Checked heat exchanger for deterioration. Checked refrigerant charge and fans on a 7-year-old American standard furnace. Cleaned and cleared drain lines and pans. Checked for adequate airflow. Changed air filters. The furnace is now operating as it should.
estimate for a new lennox system, ac and furnace, variable speed. high efficiency to save on utility bills and increase comfort.
clean and check inspection on a carrier furnace. changing filters and upgrading electronic air cleaner for cleaner air.
replacing a leaky hot water heater with a new tankless water heater installed
changing filters and preventative maintenance on a lennox furnace. servicing ao smith water heater too
service call for lennox furnace. the heat exchanger was cracked so we replaced the unit for safety and efficiency with a lennox furnace.
performed a maintenance bi annual clean and check inspection on a trane furnace. we replaced the blower motor and clean duct work as well. happy customer.
installed high efficiency Lennox furnace and ac. variable speed. duct cleaning was completed.