Cycled and inspected 2-systems. Found #1 downstairs system in good working order. Found #2 upstairs system with a restricted drain line causing system to short cycle. Also found contactor pitted and run capacitor for outdoor fan motor weak. Cleared both drain lines, installed a new contactor, and run capacitor. Left 2-systems in good working order.