Excellent service this is the second time I used them and very very satisfied. Got same day service when I called. I rate them 5 star.
Good service, explained a lot. Unfortunately couldn’t help with air because of bad compressor. So it’s July, holiday, and weekend and we have no air, so it is hard to rate a great experience.
It is one of the best AC service out there and the people are great too
NeVin was so nice and explained everything.
Awesome. Read above for my experience with Nevon. Professional polite wears mask and shoe covers. Proud of the man!!
Good experience. Great vehicle
Drain line was restricted and tripped the float switch. We flushed and cleared the drain line, cycled and monitored the system for proper electrical, pressures and temperatures. We left the system in good running order.
Upon arrival symptom was not present. Went over the system and found a weak dual run capacitor that was causing overamping and was extremely hot. Replaced it under warranty. Cleared the drain line properly in case it was partially restricted. Pressures are in range. Left system running properly. Note: told customer to call us to call us right away if issue returns.
Cycled and inspected equipment. Found equipment off on safety switch due to a restricted drain line and condensate pump. Cleared drain and condensate pump. Left system in good working order. *note* customer purchased a 1-year 2-system maintenance program.
This does NOT come with a warranty. Installed customer supplied uv bulb.
Replaced the dual run capacitor. Left system running properly.
14.5 SEER Amana Heat Pump System air out old system replace what return air box with new fiberglass board bottom install new air handler new plenum new thermostat wire up connect drain line flow switch install Goodman condenser on existing Pad Thai downpipe in start up add 1 lb of freon 410A unit working in perfect condition
I performed a complete tune up on both systems and cleared the drain lines with coil cleaner and water. I tested all electrical components, motors and safeties. I checked the refrigerant levels and temperature differentials. C/U#1- has a dirty condenser coil on two sides. A/H#1- found the return plenum not sealed or taped, has a big gap near the filter door and sucking in attic air. I taped that down. The supply plenum is also not sealed properly. The coil has some debris ( attic insulation) in it but not too bad. Also the secondary drain pan has a lot of insulation inside and can possibly get in the float switch and not allow it to shut of the unit. I removed all the insulation. The unit has a delta T of 19Â°. The unit has no P trap on the drain line. Also the primary float switch has failed. I replaced it with customer approval. I recommend we seal up both plenums and tape down all 4 return and mastic it all. C/U#2- found nothing wrong. A/H#2- the filter door is missing and t
We inspected the system, cycled and monitored it. The system is very old from 1983 (37 years old), with very poor efficiency, wear and tear, deteriorated evaporator coil and a little low on refrigerant. The duct system is also old. I highly recommend replacing the system and duct work. The customer would like an estimate and we confirmed for tomorrow, Wednesday 7/8, for 10-12 arrival time.
On this visit I inspected two systems a mini split and a regular split system. Mini split was very low on refrigerant, is 9 years old and on poor overall condition. Customer approved to charge it up with 5 lbs of R410A to get them going but I recommend replacing the system since oil traces can be found at the drain line suggesting a leak on the evap coil. Coil and blower assembly are a little dirty. No more issues were found. Split system was also low on refrigerant added 2 lbs of R410A. Inspected all electrical components and found no issues. Evap coil picture not possible. Tested heat mode with no issues. Customer provided a thermostat for me to install but was faulty, he is going to return it, declined one of ours. Cleared the drain lines, left systems running.
Upon arrival performed maintenance. Inspected electrical to insure everything was secure and no burn marks. Cleared drain line. Recommended on a blower wheel cleaning, we moved forward on the cleaning and membership. Left system in good working order.
We resealed the duct system with spray adhesive, silver tape and mastic.
I performed a complete tune up on the ac system and cleared the drain line with coil cleaner and water. I checked all electrical components and motors, refrigerant levels and temperature differentials. The condenser fan motor is overamping and the capacitor is starting to go weak. We will need to replace on our next visit ( it's a 45/5 reading 42.23/4.87). My refrigerant levels are good and I have a delta T of 21.5Â°. I loaded my pictures to service titan and left the system in proper working condition. I renewed the membership for the customer.
Performed tune up on both systems. Inspected all electrical components and found no issues. Reminded my customer about the issues with the twisted suction line at the upstairs air handler. Cleared the drain line. Left systems running.
Upon my arrival found the blower fan motor har failed. We put in a rescue motor and a new turbo mini capacitor. We checked all electrical components and motors, cleared drain line and checked our temperature differentials and refrigerant levels. Found indoor units a impacted blower wheel. The condenser has a pitted contactor and the unit is low on refrigerant r22. My delta T is at 10Â°. The customer declined any other repairs due to him replacing the system with us, so please call him in the morning to set up an appointment for Brian to come out and give him an estimate for replacement. Also let Brian know the customer is interested in a Economy UV light and maybe a surge protector for the new system. I signed him up to our senior membership program as well. Please credit today's repairs to the new system. Customer also had a 25$ coupon.
I cycled and monitored the system for proper pressures and temperatures. Itâ€™s overcast and about to rain. Itâ€™s not the best time to check the pressures, but I measured 56 degree supply temperature at this time. I recommend coming back during the early afternoon to recheck the pressures. Customer informed me the evaporator coil was replaced last year. The duct system is not in the best shape and lose of efficiency. Customer would like a quote for the duct system replacement.