Jason came when needed and was comprehensive in determining what was wrong with our hvac. I have confidence Total Air will keep our systems running. Thank you.
Raiko is very Acknowledgeable and friendly great service.
Another great service by Total
I've had 2 calls from Brian with Total Air and he's unfailingly efficient, pleasant and timely.
Our air conditioner wasn’t cooling properly and it was a Sunday. To my surprise Total Air was able to come out to the house and diagnose the problem. Brian found the problem fast and did the repairs really fast, thank goodness we just needed Freon. We’ve been with Total Air for almost 2 years now and couldn’t be more happy with the company and all the friendly people. I highly recommend this company!
Brian came out to fix our air conditioner that had a clogged drain line. He was very friendly and knowledgeable. He repaired it quickly at a reasonable price. The scheduling process was very simple, and they got someone out right away. I would definitely use Total Air again!
Upon arrival found system running. Monitored system and it stayed running. He asked that we change the 24volt fan relay just to be on the safe side and we did. Inspected the system after. Left system in good working order. Signed up for a membership.
Uppon my arrival I found the unit was low on charge after 3 weeks. The leak stop didn't seal up the hole. I think there are multiple leaks. We will need to replace the unit. Office please contact the customer to set up an appointment for Cory to come out and give them an estimate to replace. I filled the system up with r427a refrigerant out of jug #62. Just so they have air this weekend. I left the system cooling. Please credit today's repairs towards the new system.
Upon arrival found that the evaporator coil had burst and released all the freon to the ductwork. Due to being a 15 year old r22 system recommended a system replacement. Corey is scheduled to come over Monday morning. Customer rented two portable units 1 and 2. Left system off at the breaker.
Upon arrival found failed 45/5 MFD capacitor. Recommended on replacing and we moved forward. This system is very old and mismatched. Itâ€™s not running efficiently and she is aware that itâ€™s on its last leg. She is going to wait to replace it intimidates the cooler months. Left system in working order.
Started mini split install will return tomorrow to continue workingInstalled 2400 BTU three zone mini split daikon removed old condenser replaced with mini split condenser perform start up procedures and insured system was working properly pictures included customer paid in full
Install new 12 BTU unit n dining room / kitchen install new 7 BTU unit in laundry room run line hide copper drain line and communication wire wall Longhouse down to condenser unit condenser unit set on top of pad brick pad all unified and strapped together as one vacuumed and pressure-tested 4 Muirfield Court in sealed is it good in Pharr Road to everywhere
Upon arrival found multiple air leaks at the plenum and ductwork. There are to supply ducts that are deteriorated and collapsed that need to be replaced. Recommendations 1- replaced damaged 4" and 6" runs. 2-hung entire ductwork. 3-seal entire ductwork. Note: Follow up with Tracey on Monday for quote approval and scheduling.
Found system not cooling due to bad contactor. Replaced contactor and checked system operation. Checked pressures, volts, amps and all electrical components. Recommended membership but customer is selling condo so he did not want to move forward at this time. Left system in good working order.
Resealed supply and return plenums with tape, glue and mastic. Hung a return flex with nylon strap. Instructed customer to leave system off for 1-2 hours to allow mastic to dry. Uploaded pictures to service titan
Found system freezing due to running low suction pressure caused by very impacted air filter. Checked full operation of system. Blower motor run capacitor at full charge. Dual run capacitor at full charge. Cleared drain line. All electrical components operating properly. Removed air filter from system and achieved correct superheat/subcooling. Recommended membership with customer, declined at this time. System is ran around 68-70 degrees causing a dirty filter to freeze system rapidly. Advised it was a very low temperature to run unit at and the slightest impacted filter would freeze unit very quickly. Filter is being left out of system until customer gets a new one. Left system in good working order. Customer will go online to pay as service titan would not allow me to process payment.
Found nest shutting off due to clogged drain line tripping float switch. Blew out with nitrogen, then vacuumed and flushed with cleaner. Checked system operation. Left system in good working order
Completed system tune up. Checked pressures, volts, amps and all electrical components. Checked air filter and evaporator coil. Cleared drain and flushed with cleaner. Left system in good working order .
Cycled and inspected equipment. Found system off on safety switch due to a restricted drain line. Also found dual capacitor weak, run capacitor weak, contactor pitted, evaporator coil dirty, and air handler cabinet dirty. Cleared drain line, new dual capacitor, new run capacitor, new contactor, cleaned evaporator coil and air handler cabinet in place. Installed a new pure air x whole house germicidal unit. Left system in good working order.
I performed a tune up. I checked pressures, electrical components and flushed drain line with cleaner.. The blower wheel is impacted with growth and the air handler is contaminated with growth. The evap coil is dirty at air handler. The condenser is corroded from the salt in the air. The contactor is pitted/ burnt. I went over on what going on. We discussed different options. The office will call to set up appointment to give an estimate on mini splits which they are very interested in.
I performed a maintenance. I checked pressures, electrical components and flushed drain line with cleaner. I replaced pitted/ burnt contactor. I left the system in good working order.