Tabatha took my call with AC unit just stopped that is 8only 3 years old. She got me on the schedule right away. Brian came out quickly assessed the issue showed me the cost and we were on our way. Best customer experience I've had across any industry. Will be recommending Total AC to my entire family.
Brain is great.... A real professional
Have used Total Air in the past and will continue to do so!
I will recommend Total Air in a heartbeat 💓.
Outstanding service. Immediate response. I am grateful
I performed a maintenance. I checked pressures, electrical componants and flushed drain line with cleaner. I replaced pitted/ burnt contactor and weak dual run capacitor. There is a little growth inside the air handler. I recommend on installing a uv light. I left system in good working order..
Upon arrival found variable speed blower motor failed. Then found the capacitor at the condenser reading low MFD, and the contactor all pitted and burnt. Gave estimate on replacing parts and we moved forward. The capacitor comes with a 5 year warranty. Left system in good running order.
I replaced blower motor on #1 furnace, tested operation. System #4: I replaced bi flow filter drier, pressurized, evacuated and weigh in charge to factory specs. I do recommend on installing the surge protectors to prolong the systems from surges and voltage fluctuation which happens a lot. I left systems in good working order..
Upon arrival performed maintenance. Instected systems coils, pressures electrical components, and filter. Cleared out drain line. Found the 45/5 MFD capacitor at the condenser was reading extremely low. After showing we moved forward on replacing. The capacitor comes with a 5 year warranty. Left system in good working order.
I performed a maintenance. I checked pressures, electrical componants and cleaned drain line with cleaner. The existing surge protector failed, replaced. The dual run capacitor was weak of MFDâ€™s, replaced. They have a one year senior care agreement.. I left system in good working order..
Upon arrival found compressor not running. Found failed 35+5MFD capacitor. Also found burnt and pitted contactor. Recommend on replacing these parts, we moved forward. Spoke about a surge protector, we didnâ€™t move forward on installing that. After getting the system up and running I performed a maintenance. Left system in good working order.
Upon arrival performed maintenance. Inspected system and system operations. Checked pressures, electrical components, Coil, and cleared out drain line. The dual run capacitor at the condenser is reading low. It is supposed to be reading 35/5 it is reading 33/4. Due to this part reading lower than its allowance it can fail at anytime. Recommend on replacing. Got ahold of Bonnie and we moved forward on replacing the capacitor. Left system in good working order.
I performed a maintenance. I checked pressures, electrical componants and vacuumed drain line. Inside the air handler their is growth. Tomorrow I am returning to sanitize and install a pure airX with oxidizer. Irma will like a quote on a 20â€x20â€ FBG. I can install the filter back return grill tomorrow too. I left system in good working order..
Upon arrival and started the tune up, the condenser wouldnâ€™t turn on. I checked and found the system was low on refrigerant and the condenser is off from the pressure switch. The airhandler is located in the attic and the evaporator coil is frozen. I turned the system off and turned on the fan at the thermostat to thaw it out. We will have to come back in a few hours (about 12 noon) when the system is thawed out and perform a leak check. I informed the customer about what I found. They have been here for a year and the system was installed before they moved in. Returned and the system was thawed out. I performed a leak check and the evaporator coil is leaking (non repairable). System is under warranty and the evaporator coil needs to be replaced. Customer approved the work for tomorrow morning. Materials needed: evaporator coil, recovery machine, recovery tank, ply board for the attic and a fan (attic is very hot), 5 lbs of R410A Recovered what refrigerant was left in the system. R
I found no refrigerant in the system, the dual run capacitor failed and the breaker is tripped. The system is from 1992.. The system is in really poor shape. I talked to Daren the LL. He paid $79.95. If you move forward on replacement, we will credit the $79.95. I set up appointment with Stacy for Bill to come out @4pm.
We replaced both breakers and one UV light bulb. The first UV bulb was wrong and we had to go to Vicktors to purchase the right one. The customer wanted to get 2 bulbs so she had a back up. I used my company credit card. I replaced the UV light and made sure everything is still working properly. Left the unit in good working condition. I loaded pictures and my PO's to service titan and collected a payment.
I replaced the contractors and run capacitors. I noticed system #4 is starting to freeze up at evap coil. We need to possibly get to this sooner than the motor.
I found the condenser was tripped on High pressure switch, reset. The cause was that contractors working on the chimney covered the top of the condenser, set off on safety high head. The condenser fan blade is bent due to pieces of cement debris falling inside the unit. The condenser is shaking which will fail out the fan motor. The fan blade will be a warranty part, not labor. The contractor is pitted/ burnt due to safety head pressure switch setting off intermittently as it was covered. I found the pull out on disconnect is burnt up too. I put a quote together on repairs. They are interested in the pure airX to be installed in air handler. I will sanitize inside the air handler and install uv light in supply plenum..
System #1: found old bad disconnect box at condenser, replaced. I recommend on replacing the other box which is rusted out and old. This should of been done at install. The condensers have no isolation pads underneath both condensers. Later on the metal on metal will cause condenser coil leak.
I found the condenser fan motor was over amping, the contactor was pitted/ burnt, the dual run capacitor was weak on MFDâ€™s, replaced parts. I sanitized the air handler of growth and installed a pure airX uv light. Dawn will like to have a electronic air cleaner which I measured and add an extra pure airX uv light in return. I will wire into the ballast. The ballast has a life time warranty, bulbs have a 2 year warranty.