We got our 2 A/C Units replace in one day. That is a spectacular feat. They took our old ugly dirty units air handler and roof top compressor units and put in 2 new beautiful units quickly. They were very organized and came on time and even were finished early. They organized a crane company to show up when they needed to hoist the new units up and remove the old off the roof. They also put carpet and hardwood protection down so there was not harm or dirty floors left behind. Very satisfied and it was money well spent.
My “go to” company for real estate transactions, great to work with!
My A/C went out on Friday afternoon(of course) but Jon came out and worked quickly and diligently for two hours well into the evening. Identified a bad breaker that was caused by the solar installers beforehand. Very efficient, very fast, very professional.
It’s my first time with this company.great service prices are reasonable
Professional organized and efficient
The guys at total air were awesome. The crew showed up when they said, did a great job installing our new ac unit, informed us of the next steps to take and we’re all really nice
Pulled out 12’ crushed flex from underneath mobile home, replaced with all brand new 12in flex trunk line return to the unit. Should be able to to return a noticeable amount of air back to the unit, way better than before!
Upon arrival customer told me the thermostat is saying the humidity is to night. I took a temp split and checked coil and filter and it is in perfect range. Put gauges on the system and the number are in perfect range. System is running good with no issues.
Units in good running order at this time couldn’t find or hear the noise it could be a fan motor going bad
Upon arrival customer told me the ac was not cooling the house down. The evap coil is clean. The unit inside and outside where running. Put my gauges on it. Add 5 pounds of 410A. Customer just wanted me to charge the system because he is selling the property with in 6 months.
Please blower motor formodel# aspt37c14ac serial# 2003448818 customer would like a spot cooler if it’s available he also wants to order more eac filters 20x20
Re Build Supply Plenum. Customer would like to upgrade duct size in master bedroom to 7” from 6” schedule early in the day to avoid heat. Plenum turned out very nice.
Upon arrival customer told me the ac was freezing up. Turned unit on and out side kicked on but nothing inside side. I found a bad board and a variable speed ECM motor bad.
Upon arrival Customer showed me the units and thermostat after cleaning the drain pan and drain line I inspected all the electrical connections and checked the amp draw and puron pressures the system has active uv protection and a surge protector changed the filter and wiped down the cabinet with anti bacterial rag and working proper at this time
Arrived at customer's house for no cool. On arrival hooked up gages and pressures and readings all seem to be low. Showed this to customer and suggested we add freon. Customer agreed. Added 2 pounds of freon. Pressures and readings look to be of good range now. Unit putting out propper Delta T. checked in with customer and customer was pleased. Collected payment and signature for work performed and left. Customer happy.
Customer add bad condenser fan motor. After standing and oiling up the old motors still could not get disattached from shaft. Told us to customer and inform them we would have to come back with the fan blade. Customer would also like consultation. As available after 3 PM. Collected payment and signature for today's work and left. Customer happy.
Arrived at customer's house for no cool. On arrival customer showed me to air handler unit. Condensate pipe had come loose from unit. Gave customer price to repair and customers agreed. Installed new male PVC fitting fitting and new section of condensate line. Sucked out drain line. Unit now running. Giving acceptable delta T. Told customers I am not extremely confident in female futting on drain pan.. appears to have been cross threaded in past. Collected payment and signature for today's work and left. Customers happy.
Arrived at customer's house for no cool. On arrival customer told me he had drain issues earlier. He had clear drain line. Float switch was stuck on closed. Bypass float switch and unit turned on. Brought this to customer's attention and customer knowing they have secondary float switch opted to not replace float switch. Went out to condenser and hooked up gages. Pressures were not changing. Checks capacitor and capacitor was well below acceptable range. Told this to customer and suggested we get capacitor changed. Customer agreed. Changed out capacitor and unit now running fine. Talk to customer about taps plan and customer decided to sign up. Collected payment and signature for work performed and left. Customers happy.
Arrived at customer's house for system cooling Unefficiently. Hooked up gauge's to system and notice system low on freon. Check evaporator coil and evaporator coil was freezing over. Talk to customer about adding free on and customer agreed. Added 4lbs unit now looks properly charged. Customer aware he has a leak and would like to do his own leak search. Collected payment and signature and left. Customer happy.
Complete low pressure switch replacement. Recover all refrigerant from system. Remove old switch. Install new pressure switch. Remove bypass. Pressure test the system with nitrogen to ensure no leaks. Vacuum down system to 500 microns to ensure a clean line-set. Cycle and inspect equipment. Unit is in normal operating condition.