Thanks again for great service. My wife and I will surely recommend you to anyone who needs thia type of service, Thanks. HPD
No matter which technician Total Aire sends out, they are all 100% friendly, professional and knowledgeable!! Highly recommended!
Same day service, tech was friendly and informative. Thanks so much!
We called in the morning and the technician was able to come about 3 hours later. The technician was professional and very pleasant. Problem fixed within no time and I even got a small discount due to a coupon
Rigo is very good and I will recommend everyone at Total Air!
I found variable speed motor/ module failed. The system was iced up. I shut stat off. We need to check if the system is under warranty. I gave two quotes with warranty/ with out. We need to let them know once we find out.
Completed member tune up #1. I replaced the uv bulb and left the system in good running order. I filled out the check for the customer and dot signed because she broke her wrist.
I found the compressor is grounded out. The system is from 1998. Need to replace the system. We went over options of types of systems. Lennard is interested in mini splits... Bill is coming out tomorrow @ 2-4 appointment..
I performed a tuneup on both systems. I added 1 lb of 410a to the 1 st fl system. I checked electrical componants and flushed out drain lines with cleaner. The 2nd fl air handler had growth all inside. I sanitizes / wiped inside and installed a economy uv light to prevent growth from growing inside the air handler. I left the systems in good working order....
I completed a category 3 tune up on the whole system. I cleared the drain as well. A/H- my delta-T was at 20Â° with supply temperature of 54.3Â°. Found that pure X UV light bulb needed to be replaced, customer said it's been over two years. J went ahead and replaced it for him. The capacitor is starting to go weak. ( it's a 7.5 mfd road 7.17 mfd). C/U-fan motor is slightly over amping. (Amp draw was .83 and its rated for 0.8 amps.) Everything else checked out to be in proper working condition. I left the system in proper working condition.
The EAC media pads are the wrong size (20 x 20). The correct size to order is 23 x 20. Inside the coffin box is very dirty and caused the EAC media pad to get filthy very fast. We installed the system in May. I informed the customer that I will talk to Jason about what we can do. Either clean the inside of the coffin box or reinsulate it with duct board. Delivered and installed the media filter.
Install a new make up air vent for kitchen exhaust hood. Installed vent,damper and all metal pipes for it. Left the hood working properly along with the damper.
Upon arrival I found the breaker for the airhandler was turned off. Customer informed me that her husband turned it off. I turned on the breaker and activated the system for cooling mode but it was energized for heat mode. The defrost control board failed because a dead lizard short it out. We replaced this defrost board back in July. Customer had to pay for new warranty board because we are not at fault per the office. I picked up a new defrost board and replaced it. I cycled and monitored the system, checked for proper amps, voltage and temperatures and left it in good running order.
Upon arrival found the tubin of condensation pump was cutted. The piece on the pump where we connect the pump was cut too. I was able to install the tubing but if it leaks from ther he needs to replace the pump. Left the pump working properly with out leaking. Evap coil looks like got clean. We did not cleaned it.
I found the system is about 2 to 4 lbs low on 410a refrigerant. The condenser coil is impacted. Needs a chemical clean. The dual run capacitor is slightly weak and rusted out. The inside of the air handler has growth. I recommend a uv light. I gave two options on the uv lights. The ductwork needs to be sealed in the attic. They will like to move forward on condenser cleaning, add refrigerant and dual run capacitor. Need to set up appointment...The owner is a veteran, so they will like to see if we can give a discount on the uv lights and ductwork sealing.
We installed the new mini split one head very well, we ran the line set inside the attic and the core wire as well, we sealed all voids , we left and the unit running on perfectly order
I replaced the defrost control board, cycled and monitored the system in cool and heat mode, checked for proper voltage, amps and temperatures and left the system in good running order. I called Nick to let him know the system is back to normal and collected payment.
Hung and seal with mastic 3 runs and hung the mixing box. We pumped down system, replaced evap coil, re pipe section at air handler,pressurized, evacuated to 500 mc. We performed the start up procedures. I added 4 lbs of 410a.
The mini split was low on refrigerant. I added 1 lb of R410A, cycled and monitored the system and left it in good running order.
Replace evaporator coil due that when I took the existing one was worse than we thought. Relocate the line set and drain line, now customer is able to install the filter at AH. Installed a new flex and sealed the duct system. Replaced the filter drier, pressure test the system evacuated it. Left the system working good for now. Explained to the customer that pressure are good at the moment but we will make sure that is perfect at the summer visit when is hot outside. If we need add freon at that poin will be another charge. .