Upon arrival customer showed me an ac unit in the closet that needed tuned up. The evap coil is clean. Cleaned the condensate with water and nitrogen. Checked the system for proper amps and volts. Went to the condenser and Checked the system for proper amps and volts. Found no insulation on suction line and low voltage wire was bare. Customer is selling the house so wanted to make are part would not fail inspection.