Maintenance 1 Completed maintenance on a strait cool split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Heat kit tested ok. Both capacitors tested ok. Cleared drain. Pressures at normal levels. Home owner signed up for TAPS maintenance program. Homeowner purchased a pure x uvc light with free air Handler cleaning. Thia is installed and tested. Installed float switch on secondary drain port. System clean, sanitized and operating properly at this time.