Upon arrival found pressures low, performed leak search. Found leak in condenser coil. We need to call to quote on the condenser coil. Once they have the price they might want Corey to come out and give and estimate on replacement due to cost. They wanted us to add refrigerant. Added 3 pounds of 410a refrigerant. Left system in working order.