Upon arrival customer showed me a ac unit that needed to be tuned up. Checked the evap coil and it was clean. Replaced customer supplied filter. blower is clean. Checked all amps and voltage. The UV bulb is burnt. Cleared the condensate with nitrogen and solvent. Check the condenser. All amps power and Freon level. Everything is working ass it should. Replace UV bulb under Warranty.