Attic Upon arrival customer showed me an ac unit in the attic that needed to be tuned. The evap coil is clean. Cleared condensate with nitrogen and solvent. Checked the system for proper amp and voltage. Went tot the condenser checked the system for proper amp and voltage. Found the 45/5 capacitor week. Replaced it with a Turbo 200. The contactor had a little burn marks and customer Denied. Also the compressor is over amping. I recommend a hard start and customer Denied. 19 degree delta T Mini split The evap coil is clean. Used shop vac to clear condensate drain. Checked the system for proper amp and volt. System is running at a 18 degree delta T.