Customer is concerned about unit not cooling properly. Checked blower motor operation and inspected equipment cabinet. Checked thermostat calibration and filter location. Checked refrigerant levels and check test start up components. Located bad capacitor in condenser unit. Warranty capacitor. Replaced bad 40/5 capacitor and checked operation. Unit is cooling well and drains at this time. Gave new membership folder. Customer is satisfied.