Maintenance Checked all electrical components for proper volts and amp draw. All components are within factory spec. Corrected loose common wire connection. Dual run capacitor tested 42.3 of required 45. This is still considered good. Cleared drain line. Changed out EAC filter for the homeowner. System pressures are at the correct levels. Cooling temps are normal. Replaced pure x uvc bulb that expires this month. Homeowner renewed maintenance membership today. System operating normally at this time.