Arrived at customer's house for system cooling Unefficiently. Hooked up gauge's to system and notice system low on freon. Check evaporator coil and evaporator coil was freezing over. Talk to customer about adding free on and customer agreed. Added 4lbs unit now looks properly charged. Customer aware he has a leak and would like to do his own leak search. Collected payment and signature and left. Customer happy.