Arrived at customers house for system inspection. On arrival customer showed me to air handler unit. Open up cabinet and saw bio girls on top of evaporator coil. Under evaporator coil is clean. Gross on the motor housing. Next went up to condenser and hooked up gauges. All pressures in readings were a satisfactory range. Contactor sending proper voltage. Capacitor with in acceptable range. Unit was amping high on Startup. Pointed this out to customer and suggested hard start kit. Customer agreed. Installed hard start kit. Unit now starting up much easier. Check in with customer and customer was pleased with work done. Collected payment and signature and left. Customer happy.