Arrived at customer's house for no cool. On arrival hooked up gages and pressures and readings all seem to be low. Showed this to customer and suggested we add freon. Customer agreed. Added 2 pounds of freon. Pressures and readings look to be of good range now. Unit putting out propper Delta T. checked in with customer and customer was pleased. Collected payment and signature for work performed and left. Customer happy.