Excellent service and on time
Excellent support and customer service
Upon arrival customer showed me an ac unit in the closet that needed tuned up. The evap coil is clean. Cleaned the condensate with water and nitrogen. Checked the system for proper amps and volts. Went to the condenser and Checked the system for proper amps and volts. Found compressor over amping on starting. Installed a hard start. Recommend to customer to get a quote do to age and customer declined at this time
Completed member tune up visit #1. Cycled and inspected equipment. Found dual capacitor weak, contactor pitted, and air handler cabinet contaminated with bio growth. Customer approved all repairs and rescheduled work for later this afternoon. Left system in good working order for now. Returned andd installed a new dual capacitor, contactor, and pure air x. Left system in good working order.