Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Cycled and inspected equipment. Found system low on R410a. Added 3 lbs R410a and leak searched system and found leak in aluminum section of condenser coil. Left system cooling for now. Recommend: new condenser coil ( warranty 2-techs ) liquid drier, 3 lbs R410a, and recovery equipment.