Customer concerned about unit not cooling properly. Diagnostic of the txv. The txv is working properly and unit is cooling well. Possible low refrigerant charge. Located low refrigerant charge in system. Added 1 lb refrigerant to condenser unit. Cleaned vacuumed drain pan and drain line. Checked unit operation and refrigerant pressure. Unit is cooling well and drains at this time.