Televised ducts under slab floor. Ducts are concrete ducts with metal fitting and connections. Tee connection in laundry room area is heavily rusted as is the plenum. Other metal fittings look good n good condition. Concrete pipe is solid except for the area by the front door where pea gravel is entering g due to Duct dropped at that area. Suggest spin casting tee and plenum then spray lining all ducts to encapsulate the concrete.
We are applying our second application of the rubberized duct lining product to all the underground duct work
We are encapsulating all of the deteriorated underground asbestos transite air ducts with our rubberized duct lining material. The air ducts will be completely sealed and the air in the home will be environmentally safe to breathe.
We are cleaning all of the deteriorated underground duct work in preparation for our Trenchless cast mortar process. We are going to apply our Trenchless cast mortar to all of the heavily rusted connections and elbows in the duct work. This will give them a strong structure and sand and debris will no longer enter at these points.
Televised ducts under slab floor. Ducts are concrete with metal fittings and connections. Metal fittings in front of the house are rusting and deteriorated. Suggest spin cast mortar on the joints in the front of house then spray lining the entire system with Duct Armor duct lining material.
Encapsulated underground air ducts with our environmentally friendly duct lining material.
Cleaned about 200’ of underground air ducts of a slab home that were severely rusted out, after cleaning we were able to apply our trenchless cast mortar to restructure the weak metal, finally we applied two applications of our sealing product to seal the entire underground system.
Televised air duct rusted and deteriorated
Video inspection of underground air ducts. Ducts are concrete ducts possibly transite asbestos. Ducts getting water inside with heavy rains. Homeowner needs to repair leaking gutters and the extend downspouts to reduce ground water next to house. Ducts should be spray lined to seal joint connections and also encapsulate transite pipe.
Video inspection of underground air ducts. Ducts are concrete with metal connections. Metal is showing signs of rust. Suggest spray lining ducts with Duct Armor.
Video inspection of underground air ducts. Ducts are concrete with metal connections. Connections are very rusted. Suggest Trenchless Casting new concrete connections then spray lining with Duct Armor.