Found trenchless innovations on Facebook pop up and after some investigation they were exactly who. Was looking for fixed my water issues and repaired my duct work without having to bust up floors in my house incredible...
Response from Trenchless Innovations Inc.:
Thank you for your review, Mike! We are happy our process could solve your ductwork issues for you and save you from tearing up your flooring. We are grateful for your business and we thank you for placing your trust in us. We hope you enjoy your cleaner, healthier air! Thanks again!
What a pleasure it was. I submitted a request for an estimate and was able to fit me in same day. Everything was explained to me in detail and shown me what the issue was. Great experience!!!
Televised ducts from all registers and main. Did not find any issues or sign of any dead animals or rodents.
We are cleaning all of the heavily rusted underground duct work. We are then going to apply our Trenchless cast mortar to all of the deteriorated underground duct work to give them a strong structure. Once the air ducts have a strong concrete structure, we will apply two applications of our rubberized duct lining material. The air duct system will then be completely sealed and dirt and debris will no longer enter the system.
Televised ducts under slab floor. Ducts are galvanized metal ducts that are extremely rusted and deteriorated. There was no water at time of televisi g but it appears it is entering in the plenum area the traveling g through the system from there. Suggest installing a sump pump in the garage to control the water level. After that the du cts should be spin cast mortared and the spray lined with Duct Armor duct lining material.
Encapsulated all underground asbestos transite duct work with our rubberized duct lining material.
Installed a spot repair liner on the sewer from an outside clean out to seal a bad glue fitting that had roots growing into the pipe which kept causing the sewer line to back up.
Video inspection of a sewer line for a customer who is experiencing frequent back ups. Found roots growing in on the upstream side of the outside cleaned out. Propose to install a short line or to seal off the roots.
Video inspection of a sewer from an outside clean out. The 4” cast iron has a slight separation on the top of the pipe just upstream of the clean out. The problem is not urgent but should be taken care of in the future. Trenchless Innovations suggests installing a small spot line between the house and the clean out.
We looked at some above ground duct work for a home owner who bought a house from a heavy smoker, they had gone through major work to get rid of smoke odor, prime/painted entire house, replaced carpets and flooring, even had duct work cleaned, and still the odor remained! We spray lined the entire air duct system supply/return lines to encapsulate duct work to eliminate smoke odor in HVAC system, so now the air flows through new sealed system.