Televised ducts under slab floor. Ducts are concrete possibly Transite with metal connections and fittings that are rusting and deteriorated in the front of the house. There are drainage issues with downspouts and a retention wall that could be contributing to the deterioration in the front of the house. Suggest making changes to the landscape and downspouts then spin cast mortaring the metal fitting and spray lining the system with Duct Armor duct lining material.
Televised ducts under slab floor. Ducts are concrete with metal connections and fittings. There was only a small amount of pea gravel in the ducts but not enough to restrict any air flow. Believe the reduced air flow to bedroom is due to the configuration of the system. Suggest spray lining the ducts with Duct Armor duct lining material to encapsulate the concrete asbestos ducts.
Televised ducts under slab floor. Ducts are spiral wound ducts showing heavy signs of rust and deterioration. There is standing water in the plenum. Ran water in kitchen bath and laundry and could not get water to move so it appears to be ground water. Suggest installing outside sump pit and pump to try to lower the water level. Could try at first. If necessary we may have to install a leg of drain tile through foyer then into pit. After water is resolved the ducts should be spin cast mortared and then spray lined with Duct Armor duct lining material.
We are applying the second application of our rubberized duct lining material to all of the deteriorated underground duct work. All of the cracks and openings will be completely sealed and the air in the home will be environmentally safe to breathe.
We are applying the second application of our rubberized Duct Armor product to all of the underground duct work. The entire underground air duct system will be completely sealed and the air in the home will be environmentally safe to breathe.
We are applying our Trenchless Cast mortar to all of the heavily deteriorated underground duct work. This process will give the old air ducts a strong and sturdy structure. We are now going to apply the first application of our rubberized Duct Armor material to all of the underground duct work to completely seal the system.
Repairing underground duct work using Trenchless Casting to repair the metal corners and connectors. Sealing the entire system with are duct lining material.
Televised ducts under slab floor. Ducts are concrete with metal connections. Metal connections are rusted at bathroom tee and plenum and need to be spin cast. After that the system should be spray lined with duct armor. Customer also needs to repai gutters and extend downspouts around house.
Televised underground ducts in slab home, customer was getting water in back of home ductwork. Recommend reconfiguring downspouts and sealing and encapsulating system with Duct Armor.
Encapsulated heavily rusted underground duct work with our duct lining material.
Applied trenchless cast to all bad metal joints and fittings to restructure in preparation to seal with our duct lining product
Cleaned all the underground duct work under a slab home and encapsulated 160’ of transite pipe.
Cleaned all underground duct work under the slab home and applied our duct lining product to encapsulate and seal the duct work.
Televised ducts under slab floor. Ducts are PVC with metal elbows and connections. Most of the system has standing water in it. Plenum in heavily rusted and has water in it. Downspouts need to be extended away from the house. The property should be regarded to allow water to flow away from the house. Once the water issue is resolved the ducts should be spray lined with Duct Armor duct lining material.
Video inspection of underground air ducts. Ducts are concrete with metal connections and fittings that are rusting. Plenum under furnace is also very rusted. Suggest spray lining system with Duct Armor duct lining material.