Televised underground ducts in slab home, customer was getting water in back of home ductwork. Recommend reconfiguring downspouts and sealing and encapsulating system with Duct Armor.
Encapsulated heavily rusted underground duct work with our duct lining material.
Applied trenchless cast to all bad metal joints and fittings to restructure in preparation to seal with our duct lining product
Cleaned all the underground duct work under a slab home and encapsulated 160’ of transite pipe.
Cleaned all underground duct work under the slab home and applied our duct lining product to encapsulate and seal the duct work.
Televised ducts under slab floor. Ducts are PVC with metal elbows and connections. Most of the system has standing water in it. Plenum in heavily rusted and has water in it. Downspouts need to be extended away from the house. The property should be regarded to allow water to flow away from the house. Once the water issue is resolved the ducts should be spray lined with Duct Armor duct lining material.
Video inspection of underground air ducts. Ducts are concrete with metal connections and fittings that are rusting. Plenum under furnace is also very rusted. Suggest spray lining system with Duct Armor duct lining material.
Video inspection of underground air ducts. Ducts are concrete possibly Transite with asbestos. Metal fittings are heavily rusted. Suggest spin cast mortar of metal joints to restore the structure and then spray lining the system with Duct Armor duct lining material.
We cleaned all the underground air ducts, then applied our trenchless cast to all the underground duct work to give weak rusted metal a strong structure, and finally applied two applications of our duct lining product to seal the entire underground system.
Vonorction of underground air ducts. Ducts are extremely rusted and deteriorated ducts need to be restored by Trenchless Casting a new concrete pipe inside the old ducts then spray lining the ducts with Duct Armor
Video inspection of underground air ducts. Ducts are metal and extremely rusted and have some standing water in one of the pipes and in the plenum under the furnace. Suggest Trenchless Casting a new concrete pipe inside the old pipe to restore structure to the pipe. After that the ducts should be spray lined with Duct Armor.
Video inspection of underground air ducts. Ducts are extremely rusted and are getting water at times of heavy rains. Customer needs to extend all downspout away from the house. After that they should get the ducts rebuilt with Trenchless Casting to restore structure and the spray lining ducts with Duct Armor.
Completed second application of Duct Armor to encapsulate and restore under slab duct work. We give a 15 year transferable warranty.
Televised underground duct work they were transite pipe(which may contain asbestos) with metal connectors and elbows. Also found minimal water in plenum box under furnace which is the lowest point in the system, so we recommend to run down spouts farther out away from house to eliminate water from getting under the slab and in the duct work. Once the down spouts were extended out and ducts were dry we were able to apply our duct armor product to encapsulate the transite pipe and seal the system.
Video inspection of underground air ducts. Ducts are transite asbestos pipes and should be spray lined to encapsulate the pipes.