Duct lining application service call. Applied first coat of Duct Armor to all registers and duct runs.
Sewer inspection service call. Televised sewer from inside clean out. Could only push approximately 104ft due to configuration of clean out and the turns it made. Clay tile up to that point looks to be in good condition. Sewer repair recommended. Suggest installation of and outside clean out then re-televise for possible lining. Recommend Bills Plumbing for installation of clean out.
Televised and cleaned all underground ductwork. Coated all underground ductwork with duct armor and transite pipe in basement.
Televised ducts under slab floor. Ducts are mostly clay tile with the exception of one run that is metal. The one metal run is extremely rusted and deteriorated. The clay tile has debris at the joints. Suggest spin cast mortaring the system then spray lining with Duct Armor duct lining material. Customer has just recently installed drain tile around entire house to control any water issues.
We are applying the second application of our rubberized Duct Armor material to all of the underground asbestos transite air ducts. The air in the home will be environmentally safe to breathe.
We are cleaning all the underground duct work, and sealing the underground duct work, which is transite concrete pipe with metal connectors/ elbows, with our duct lining product.
Televised ducts under slab floor. Ducts are metal and are extremely rusted. Ducts should be spin cast mortared to restore the structure of the ducts then spray lined with Duct Armor duct lining material.
Televised under slab ductwork, found to be transite concrete ducts. Recommend encapsulating and sealing.
Video inspection of underground air ducts. Ducts are cardboard with metal fittings and elbows. Ducts are showing signs of water damage and also deterioration. Suggest spin casting a new concrete pipe inside the old ducts to restore structure and then spray lining ducts with Duct Armor duct lining material.
Video inspection of underground air ducts. Ducts are concrete possibly Transite asbestos pipes. Suggest spray lining the ducts with Duct Armor duct lining material to encapsulate the asbestos pipes.
Video inspection of underground air ducts. Air ducts are galvanized metal. Metal shows slight signs of rust and is allowing dirt to enter into the system through the joints. Suggest spray lining the system with Duct Armor duct lining material.
Video inspection of sewer line from an outside clean out. Sewer has heavy roots and an area that is leaking and causing a sink hole. Suggest installing a sewer liner in existing pipe through the clean out to seal the pipe and stop the root growth.
Video inspection of a sewer from a basement clean out. Sewer is clay tile with heavy root growth throughout. Suggest installing an outside clean out and then installing a liner in the sewer to repair the remaining 80 ft of sewer.
Video inspection of underground ducts.