We are televising underground pvc air ducts that have water throughout the system. We are going to look at all of the water issues and give the customer a solution for the problem.
Televised ducts under slab floor ducts are concrete ducts with metal fittings and connections. Due to elevated radon levels in the house suggest sealing the ducts by spray lining ducts with Duct Armor duct lining material.
Televised ducts under slab floor. Ducts are pvc with metal connections. There had been a sewer break that had contaminated the line. Suggest spray lining ducts to encapsulate.
We are cleaning all the underground duct work, installing a 3’ spot repair liner in the main line where a breach in the pipe was allowing the gravel back fill to fall in and block air flow off for the bedrooms, and also sealing the entire underground duct work with our duct lining product.
Televised ducts under slab floor. Ducts are galvanized metal and showing slight signs of rust. No water was visible in the system at the time of inspection. Customer needs to extend downspouts away in the back of the house and also inspect gutters for proper flow. Suggest spray lining ducts with Duct Armor duct lining material.