Slab leak detection service call. Televised ducts under slab floor. Ducts are cardboard ducts. The run in the family room has dropped and is no longer lined up. Will provide proposal for blocking off the space around duct and then spin cast mortaring and duct lining.
2-14-2023: Cleaned and measured in preparation for lining, did not install spot repair liner at 24’ mark used pan and tilt camera to verify its not a break but a cross connection and need to get OK from city that the tie in’s are dead and can be lined/ covered over. 3-31-2023: installed spot repair liner over cross connection in street before city main where pipe was heavily cracked and had heavy root growth, also lined 6” clay sewer 35’ to city main starting liner in 6” pvc just downstream of clean out and ended liner in 6” clay just before city main.
We are applying the first application of our rubberized duct lining material to all of the underground asbestos transite air ducts.
Rebuilt all register vents with hydraulic cement. Applied first application of duct armor to all underground ductwork.
Televised ducts under slab floor. Ducts are concrete ducts with metal fittings and connections. Provide proposal for spray lining ducts with Duct Armor duct lining material.
We are applying the first application of our rubberized duct lining material to all of the rusted underground galvanized metal duct work.
Televised ducts under slab floor. Ducts are PVC with metal fittings and connections. No standing water at the time of inspection but there were water marks indicating water has been in the ducts. The elbow under the foyer from the vent near the front door is broke allowing stone to enter the ducts. This would need to be dug to be replaced. Downspouts need to be extended all around the building and some type of retaining wall installed to prevent water from accumulating next to sliding glass door.
We are televising underground pvc air ducts that have water throughout the system. We are going to look at all of the water issues and give the customer a solution for the problem.
Televised ducts under slab floor ducts are concrete ducts with metal fittings and connections. Due to elevated radon levels in the house suggest sealing the ducts by spray lining ducts with Duct Armor duct lining material.
Televised ducts under slab floor. Ducts are pvc with metal connections. There had been a sewer break that had contaminated the line. Suggest spray lining ducts to encapsulate.
We are cleaning all the underground duct work, installing a 3’ spot repair liner in the main line where a breach in the pipe was allowing the gravel back fill to fall in and block air flow off for the bedrooms, and also sealing the entire underground duct work with our duct lining product.
Televised ducts under slab floor. Ducts are galvanized metal and showing slight signs of rust. No water was visible in the system at the time of inspection. Customer needs to extend downspouts away in the back of the house and also inspect gutters for proper flow. Suggest spray lining ducts with Duct Armor duct lining material.